Presentation on theme: "741 First Avenue King of Prussia, PA 19406 Phone: 610-962-1600 Fax: 610-962-0230 www.tozourtrane.com Discussion of 3-Phase Photocatalysis A Revolutionary."— Presentation transcript:
741 First Avenue King of Prussia, PA Phone: Fax: Discussion of 3-Phase Photocatalysis A Revolutionary Technology that Cleans, Deodorizes and Disinfects the Air
Filtration has been in common use for many years – PCO is not filtration (Capture) Photolysis is understood and used in multiple applications throughout the world – PCO is not Photolysis (Cleaning/ surfaces) Photocatalysis (PCO) using a semi-conductor such as titanium dioxide (TiO²) has been known and pursued for at least twenty-five years but it had application and production constraints – until NOW! PCO produces natures soap - Hydroxyls PCO is all three… Capture, Cleaning and Conversion.
Has been rigorously tested by many certified labs, such as the Department of the Armys Dugway Proving Grounds and RTI International Mold: Aspergillus versicolor and Aspergillus niger have both been tested with similar results… Genesis Air GAP photocatalysis process averages 93.5% in a single pass removal rate with no viable airborne fungal spores. Bacteria: Bacillus atrophaeus (anthracis), Staphylococcus epidermidis (Staph), Mycobacterium parafortuitum (Tuberculosis) and Escherichia coli (E.coli) have all four been tested with the Genesis Air GAP system and were able to remove or neutralize better than 98% single pass of airborne bacterial spores. Viruses: MS2 (MRSA) was the primary virus testing agent. Dugway Proving Grounds stated no MS2 was found after each challenge. RTI International gave the Genesis Air GAP unit 2008B a 275 CARm (Clear Air Rate microbiological) rating for MS2. VOCs / Odors: VOCs like Benzene, Styrene, Toluene, Formaldehyde and Carbon Monoxide have been successfully tested reducing the level of VOCs. GAP Three step synergistic approach / Photocatalytic Oxidation (PCO) / Proven, leading-edge technology / Safe – no ozone or by-products, no accumulation of chemical contaminants; converts toxic substances to benign / Scalable - GAP can be engineered to any size air stream. Merv 13 FiltrationUVCGI Photocatalytic Oxidation Reduces Particulate and also serves to protect Germicidal ultra violet light is used to activate Patented titanium dioxide coated media HVAC equipment and the final stages of the the photocatalyst cell and provides additional when activated by UV light, creates a Genesis Air process from particulate contamination measure of bacteriological irradiation hydroxyl cloud oxidizing organic compounds, converting them into benign carbon dioxide and water vapor
STAPH Testing, courtesy of: RTI International, Research Triangle Park NC
Simulant for B.anthracis Simulant for Mycobacterium tuberculosis
Hospital-associated outbreaks usually occuring during periods of construction or renovation, when increased environmental contamination with Aspergillus species can occur. Although air contamination is often implicated, direct contamination of air-handling systems is unusual. Herein, we describe an outbreak of invasive Aspergillus infection in postsurgical patients that was ultimately traced to a contaminated air-handling system in an operating theater. This investigation of invasive Aspergillus infections among postsurgical patients identified mold contamination in an operating theater air-handling system. Aspergillus species are infrequent but serious causes of nosocomial infection. Although contamination of air-handling systems is uncommon, this outbreak suggested that some modification in current air quality guidelines may be necessary for critical patient care areas, such as oncology wards, icus, and operating theaters. Current guidelines for operating theaters only address total air exchanges per hour, air filtration efficiency, filter location, and monitoring systems to measure pressure drops across filters & air exchange rates. The routine use of airborne particle counts to monitor air quality is not currently recommended. Instead, avoidance of fungal contamination is sought through good construction and maintenance practices. Despite the appropriate implementation of these guidelines by this hospital, an outbreak of Aspergillus infection still occurred. Clinical Infectious Diseases 2003; 37:786– by the Infectious Diseases Society of America.
Cleaning surfaces and Providing energy for The Photocatalytic Conversion process
Three Types A – Long Wave Black Light / 400nm-315nm No skin damage – bug zappers, theatrical lighting, tanning booths 98.7% of the UV light from the Sun that reaches Earths surface is A Note: over 98% of UV from Sun is blocked by ozone layer B – Medium Wave / 315nm-280nm Exposure produces vitamin D in the skin – No exposure vitamin D deficiency Over exposure DNA damage (sunburn) – skin repairs by forming melanin (sun tan) C – Short Wave Germicidal / 280nm- 100 Highest energy – most dangerous
Cleaning Bio/film from coils
Mold Growth in Fiberglass Downstream of HEPA Filtration in an O.R.
The use of UVC lights in a dual role could reduce the risk of: Surface growth on coils and through the removal of bio/film lower energy cost Viable airborne mold and associated toxins, as well as Volatile Organic Compound reduction In this application UVC is used to clean surface and energize a PhotoCatalyst
PCO products generate hydroxyl radicals As shown by independent testing, these hydroxyl radical producing devices at 500fpm reduce/remove mold, bacteria and virus UV lamps alone do not kill mold in 18 at 500fpm. Another benefit is the reduction of VOCs Genesis Air Photocatalytic Oxidation GAP
Examples: Aspergillus versicolor, 500 FPM with mW/cm 2, needs 14 or 1.67 seconds to kill. Aspergillus niger, 500 FPM with mW/cm 2, needs 650 or seconds to kill. How many seconds residence time does your airhandler have? For a 2 section, at 500 FPM = 0.24 seconds mW/cm 2 is at the surface of the lamp. At 4 away from the lamp, needed residence time increases 10-fold.
Photo Catalytic Oxidation Solves the IAQ Puzzle UV Light is best used for Surface Cleaning and to Energize PCO Conversion Technologies To Clean Surfaces and Airstreams
There are airborne infections, and they have associated costs (MRSA, C. diff, TB, mold, mold fragments and mycotoxins). The use of UVGI lamps alone, while accepted to clean surfaces, will not work in airstreams due to DNA repair. The use of HEPA filters, however, may represent overkill when applied for the control of airborne microbes. In one OR test, a HEPA filter provided no better reduction in airborne bacterial load than a 95-percent dust-spot filter . Furthermore, the combination of UVGI and high-efficiency filters in the MERV-13 to -15 range may be able to provide performance virtually equivalent to HEPA filtration, thus offering health-care facilities the possibility of reducing energy costs without increasing health risks .
GAP technology has been developed to remove and neutralize harmful particulate and organic contaminants in air Testing has consistently demonstrated that the Genesis Air GAP system removes and destroys an average of 93.5% of airborne fungal spores, and greater than 98% of airborne bacterial spores The use of UVCGI lamps alone, while accepted to clean surfaces, will not work in airstreams due to DNA repair and required dwell time VOCs are dramatically reduced including Formaldehyde and Carbon Monoxide Genesis Airs GAP technology will protect system components Ideally installed after a good-quality prefilter, and before the coils and other components of the HVAC system. By converting corrosive, toxic vapors before the coils, the coils are kept clean, optimizing cooling and heating efficiency. The UVGI lamps, working together with the photocatalyst, can actually reverse contaminated buildup in the system promoting energy savings and better health The increasing cost of Nosocomial Infections is dramatic… Can you afford to do nothing?