Download presentation

Presentation is loading. Please wait.

Published byEmerson Fossey Modified over 2 years ago

1
1 EENG 224 Chapter 11 AC Power Analysis Huseyin Bilgekul Eeng224 Circuit Theory II Department of Electrical and Electronic Engineering Eastern Mediterranean University Chapter Objectives: Know the difference between instantaneous power and average power Learn the AC version of maximum power transfer theorem Learn about the concepts of effective or Rms value Learn about the complex power, apparent power and power factor Understand the principle of conservation of AC power Learn about power factor correction

2
2 EENG 224 An Electical Power Distribution Center

3
3 EENG 224 Apparent Power and Power Factor The Apparent Power is the product of the Rms value of voltage and current. It is measured in Volt amperes (VA). The Power Factor (pf) is the cosine of the phase difference between voltage and current. It is also the cosine of the angle of load impedance. The power factor may also be regarded as the ratio of the real power dissipated to the apparent power of the load. The Average Power depends on the Rms value of voltage and current and the phase angle between them.

4
4 EENG 224 Apparent Power and Power Factor Not all the apparent power is consumed if the circuit is partly reactive. Purely resistive load (R) θ v – θ i = 0, Pf = 1 P/S = 1, all power are consumed Purely reactive load (L or C) θ v – θ i = ± 90 o, pf = 0 P = 0, no real power consumption Resistive and reactive load (R and L/C) θ v – θ i > 0 θ v – θ i < 0 Lagging - inductive load Leading - capacitive load P/S < 1, Part of the apparent power is consumed

5
5 EENG 224

6
6 Power equipment are rated using their appparent power in KVA.

7
7 EENG 224 Apparent Power and Power Factor Both have same P Apparent Powers and pfs are different Generator of the second load is overloaded

8
8 EENG 224 Apparent Power and Power Factor Overloading of the generator of the second load is avoided by applying power factor correction.

9
9 EENG 224 Complex Power The COMPLEX Power S contains all the information pertaining to the power absorbed by a given load.

10
10 EENG 224 The REAL Power is the only useful power delivered to the load. The REACTIVE Power represents the energy exchange between the source and reactive part of the load. It is being transferred back and forth between the load and the source The unit of Q is volt-ampere reactive (VAR) Complex Power

11
11 EENG 224 Resistive Circuit and Real Power

12
12 EENG 224 Inductive Circuit and Reactive Power

13
13 EENG 224 If the average power is zero, and the energy supplied is returned within one cycle, why is a reactive power of any significance? At every instant of time along the power curve that the curve is above the axis (positive), energy must be supplied to the inductor, even though it will be returned during the negative portion of the cycle. This power requirement during the positive portion of the cycle requires that the generating plant provide this energy during that interval, even though this power is not dissipated but simply borrowed. The increased power demand during these intervals is a cost factor that must that must be passed on to the industrial consumer. Most larger users of electrical energy pay for the apparent power demand rather than the watts dissipated since the volt-amperes used are sensitive to the reactive power requirement. The closer the power factor of an industrial consumer is to 1, the more efficient is the plants operation since it is limiting its use of borrowed power. Inductive Circuit and Reactive Power

14
14 EENG 224 Capacitive Circuit and Reactive Power

15
15 EENG 224 Complex Power The COMPLEX Power contains all the information pertaining to the power absorbed by a given load. Real Power is the actual power dissipated by the load. Reactive Power is a measure of the energy exchange between source and reactive part of the load.

16
16 EENG 224 Power Triangle a) Power Triangleb) Impedance Triangle Power Triangle The COMPLEX Power is represented by the POWER TRIANGLE similar to IMPEDANCE TRIANGLE. Power triangle has four items: P, Q, S and θ.

17
17 EENG 224 Power Triangle Finding the total COMPLEX Power of the three loads.

18
18 EENG 224 Power Triangle

19
19 EENG 224 Real and Reactive Power Formulation

20
20 EENG 224 Real and Reactive Power Formulation

21
21 EENG 224 Real and Reactive Power Formulation

22
22 EENG 224 P is the REAL AVERAGE POWER Q is the maximum value of the circulating power flowing back and forward Real and Reactive Power Formulation

23
23 EENG 224 Real and Reactive Powers CIRCULATING POWER REAL POWER

24
24 EENG 224 Real and Reactive Powers V rms =100 V I rms =1 A Apparent power = V rms I rms =100 VA From p(t) curve, check that power flows from the supply into the load for the entire duration of the cycle! Also, the average power delivered to the load is 100 W. No Reactive power.

25
25 EENG 224 Real and Reactive Powers V rms =100 V I rms =1 A Apparent power = V rms I rms =100 VA From p(t) curve, power flows from the supply into the load for only a part of the cycle! For a portion of the cycle, power actually flows back to the source from the load! Also, the average power delivered to the load is 50 W! So, the useful power is less than in Case 1! There is reactive power in the circuit. Power Flowing Back

26
26 EENG 224 Practice Problem 11.13: The 60 resistor absorbs 240 Watt of average power. Calculate V and the complex power of each branch. What is the total complex power?

27
27 EENG 224 Practice Problem 11.13: The 60 resistor absorbs 240 Watt of average power. Calculate V and the complex power of each branch. What is the total complex power?

28
28 EENG 224 Practice Problem 11.14: Two loads are connected in parallel. Load 1 has 2 kW, pf=0.75 leading and Load 2 has 4 kW, pf=0.95 lagging. Calculate the pf of two loads and the complex power supplied by the source. LOAD 1 2 kW Pf=0.75 Leading LOAD 2 4 kW Pf=0.95 Lagging

29
29 EENG 224

30
30 EENG 224 Conservation of AC Power The complex, real and reactive power of the sources equal the respective sum of the complex, real and reactive power of the individual loads. a) Loads in Parallel b) Loads in Series For parallel connection: Same results can be obtained for a series connection.

31
31 EENG 224

32
32 EENG 224

33
33 EENG 224 Complex power is Conserved

Similar presentations

© 2017 SlidePlayer.com Inc.

All rights reserved.

Ads by Google