We think you have liked this presentation. If you wish to download it, please recommend it to your friends in any social system. Share buttons are a little bit lower. Thank you!
Presentation is loading. Please wait.
Published byAyanna Bice
Modified over 2 years ago
PowerPoint ® Presentation Chapter 8 Boiler Operation Procedures Taking Over a Shift First-Time Boiler Start-up Procedures Routine Boiler Start-up Procedures Boiler Maintenance Procedures Boiler Shutdown Procedures Boiler Inspection Hydrostatic Test Boiler Troubleshooting
Chapter 8 Boiler Operation Procedures Boiler operation information is communicated to the boiler operator starting the shift to specify any special procedures required.
Chapter 8 Boiler Operation Procedures When blowing down the gauge glass, water should enter the gauge glass quickly when the gauge glass blowdown valve is closed.
Chapter 8 Boiler Operation Procedures During a bottom blowdown, the boiler should be under light load and the water level should be at the NOWL.
Chapter 8 Boiler Operation Procedures The blowdown valve is opened to evacuate the low water fuel cutoff chamber with the burner firing during blowdown.
Chapter 8 Boiler Operation Procedures When testing the flame scanner, the flame scanner sensor is covered to simulate a flame failure.
Chapter 8 Boiler Operation Procedures Before starting the boiler for the first time, the boiler should have a minimum water level of approximately 2 above the bottom of the gauge glass.
Chapter 8 Boiler Operation Procedures The burner is started in low fire according to procedures specified by the manufacturer.
Chapter 8 Boiler Operation Procedures The boiler vent is closed when pressure in the boiler reaches 10 psi to 15 psi.
Chapter 8 Boiler Operation Procedures The main steam stop valve is opened slowly to allow the pressure to equalize when the boiler is a few pounds below the header pressure.
Chapter 8 Boiler Operation Procedures A broken or discolored gauge glass is replaced using standard procedures for maximum safety.
Chapter 8 Boiler Operation Procedures The low water fuel cutoff controls must be installed vertically for proper performance.
Chapter 8 Boiler Operation Procedures The burner is maintained and tested to ensure proper operation and maximum efficiency.
Chapter 8 Boiler Operation Procedures Feedwater pumps should be checked periodically to ensure proper bearing temperatures and checked for any unusual vibration.
Chapter 8 Boiler Operation Procedures Safety valves are routinely tested to ensure proper operation and must be serviced by an authorized manufacturer representative.
Chapter 8 Boiler Operation Procedures Steam traps are checked for proper operation when determining the cause of a steambound feedwater pump.
Chapter 8 Boiler Operation Procedures When inspecting a boiler, inspect tube sheets, tubes, and other internal parts for corrosion, overheating, and/or other damage.
Chapter 8 Boiler Operation Procedures Handhole covers are removed to provide access to boiler parts during a boiler inspection.
Chapter 8 Boiler Operation Procedures All internal surfaces are exposed and cleaned prior to the boiler inspection.
Chapter 8 Boiler Operation Procedures Troubleshooting steps from the manufacturer provide a guide to correcting a boiler operation problem.
Chapter 8 Boiler Operation Procedures The boiler room log lists boiler operation data that can be used to increase boiler efficiency and identify a potential malfunction.
Developed by Western Iowa Tech Community College This material was produced under a grant (SH F-19) from the Occupational Safety and Health.
Boilers Boiler is an apparatus to produce steam. Thermal energy released by combustion of fuel is used to make steam at the desired temperature and pressure.
Power Plant Engineering. Boilers Boilers Boiler is an apparatus to produce steam. Thermal energy released by combustion of fuel is used to make steam.
1 STEAM HEATING. 2 ) What is Steam Heating a) Steam heat is similar to hot water heat except the latent heat of the steam vapor contains a larger amount.
The Hartford Steam Boiler Inspection and Insurance Company Preventing Equipment Failures Boilers Electrical Distribution Systems Air Conditioning Equipment.
Fired And Unfired Pressure Vessels A pressure vessel is a vessel in which pressure is obtained from an external source, or by the application of heat from.
Introduction Watertube boiler construction Steam generation process Watertube boiler classification Raising steam.
1 BASIC COAL FIRED BOILER ATTENDANCE TRAINING COURSE.
Presentation Dungrani rakesh v. Div : a Branch : mechenical Sem : 1 st.
Dept. of Mech & Mfg. Engg. 1 Boilers. Dept. of Mech & Mfg. Engg. 2 Steam Boilers Definition of a Boiler Boiler is defined as a closed metallic vessel.
Boiler Mountings. Boiler mountings are nozzle connections, distance pieces, valves or fittings attached directly to the boiler and are always subjected.
Maintenance Shows of America April 2010 Tampa Florida Presented By: Byron Nichols Representing: The American Society of Power Engineers.
Module 11: Use and Care of Equipment At the HIV Rapid Testing Site.
ACTIVE LEARNING PROCESS Prepared By : Guided By : Prof. Jugal Panchal Branch: Computer Engineering RAJ PATEL ID NO:13BECEM043 YASH PATEL ID NO:13BECEM044.
International Mechanical Codes Scald Protection. – Where a combination potable water-heating and space-heating system requires water for space.
Exquisite Heat For Steam Boilers. Time based system Thermostat Demand Analysis over time will determine the length of burner fire time of the boiler.
For Steam Boilers & Hot Air, Fresh Air, et al.. Thermostat Demand Analysis over time resets burner fire time for steam boiler. This will remove the leads.
Fuel Oil Systems ► Fuel Oil Systems consist of: Storage Tanks Pumps Heaters Strainers Measuring and control devices Piping.
Prepared by :
11-1 Copyright 2010 McGraw-Hill Australia Pty Ltd PowerPoint slides to accompany Puffett, Hossack, Stone, Burn & Miles, Gasfitting 2e Chapter 11 OPERATION.
Mountings & Accessories Faculty : RAVI PATEL STUDENT NAME: (1) MAURYA ANANDRAJ J. (2) MAKADIA KULDEEP C. (3) SHAH UTSAV B.
Boilers. Boilers Boiler is an apparatus to produce steam. Thermal energy released by combustion of fuel is used to make steam at the desired temperature.
I Need A Space Heating System Let’s Look At A Central Steam Plant Option.
Student Book © 2004 Propane Education & Research CouncilPage Placing Appliances into Initial Operation Knowing the proper techniques and.
HVAC523 Heat Sources. Classification of Hydronic heat sources Conventional gas and oil fired boilers Condensing gas fired boilers Electric resistance.
CASE STUDY-III BOILER TUBE FAILURE. The Incident Boiler Make: MIURA Date: March 26, 2010 Place: At sea Initial Indication: Frequent water being.
POWER EQUIPMENT INSTRUCTOR: ROBERT A. MCLAUGHLIN ZAILI THEO ZHAO HIGH PRESSURE FITTINGS WEEK 13 01:16 1.
1 Heat Exchangers. Standards of Conduct in Training 2.
Energy Efficient Steam Systems. Steam System Energy Flows Energy enters a steam system as: –Fuel and combustion air –Makeup water –Pump work Energy.
Types of Heaters Steam Quaker Oats St. Joseph, MO.
B OILER Presented by: Muhammad Azffar Mohamad Hanif bin Yusof Nor Aminah bt. Mohd Khalil
Hydronic Mechanical Controls. Air Scoop or Air Purge 1. Located in the system (commonly on top of expansion tank 2. Has internal baffles that divert bubble.
DHHB, 1ID MAINTENANCE Effects of Cold on Military Vehicles.
Function and Types. Purpose Steam traps exist to discharge air and condensate while not permitting the escape of live steam Their goal is to ‘purify’
Engine Maintenance Chapter 5 Inboard Diesel Engines Part 2.
Lesson 7. mechanical power is produced by a heat engine that transforms thermal energy (from combustion of a fuel) into rotational energy heat (generated.
ABL-14d Able Elective Engines Instructors: George Crowl.
Number One In The World For a Reason ® ® Holmatro Hydraulic Rescue Tool What You Need to Know to Maintain your Rescue Tool System © 4/2004 Holmatro.
Boiler Mounting Made by : Group 2 Electrical Eng-B.
1B-1 Fire Engine Maintenance Unit 1B – Pump Inspections and Maintenance.
2.5.6 Student Book © 2004 Propane Education & Research CouncilPage Operating a Propane Dispenser to Fill Vehicle-Mounted ASME Tanks To safely and.
Boiler>Safety v/v>Regulations Singapore Maritime Academy/ Singapore PolytechnicKalyan Chatterjea/June Boiler Safety Valve Regulations Based on ABS.
World Leaders in Combustion Management Solutions PID Control (P)roportional (I)ntegral Internal Stat PID (D)erivative Further.
Griner Drilling Service Pump Repair and Maintenance.
Dailies, Weeklies, Monthlies, PSM Maintenance - Simplify IT If you’d like to reach SCS Engineers, Tracer Environmental Division please contact us at:
© 2017 SlidePlayer.com Inc. All rights reserved.