Presentation on theme: "Fall 201208.28.2012ENERGY MANAGEMENTLecture 2--1 Lecture 2 BrieflySolar and Wave Energy (GREEN) Book chapter 5Boilers and Fired Systems Book Chapter 6Steam."— Presentation transcript:
Fall ENERGY MANAGEMENTLecture 2--1 Lecture 2 BrieflySolar and Wave Energy (GREEN) Book chapter 5Boilers and Fired Systems Book Chapter 6Steam and Condensate Systems
Introduction to solar and wind energy This section includes discussions of renewable energy resources, but primarily those of solar and wind. At the present time the payback period is greater than other renewable's. However, as time proceeds the payback period will decrease. The payback will gradually approach the other types of energy and storage systems Fall ENERGY MANAGEMENTLecture 2--2
ULL Ocean Energy & Technology Team Dr. Ted Kozman Dr. Yucheng Liu Jeremiah Pastor –Team Leader Kelly Guiberteau Grant Caliver Raul Viera Clay Guillory Kevin Judice
Comparison to Other Estimates EPRI used spectral analysis to estimate 60 TWh/yr on inner shelf 80 TWh/yr on outer shelf Extrapolation methods were not given Used 4 buoys Further offshore had a high number of events More events offshore Classified GOM as Mildly Energetic (< 10 kW/m)
Fall ENERGY MANAGEMENTLecture 2--5
Why the GOM High Activity 4,125 platforms 2,380 companies 161 operators 561Gm 2 leases Ship Diesel to platforms Fuel cost Shipping cost Emissions cost Permit growth is spreading to deep waters.
Fall ENERGY MANAGEMENTLecture 2--7
Spring ENERGY MANAGEMENTLecture 2--8
Spring ENERGY MANAGEMENTLecture 2--10
Power Buoy Ocean Power Technology, US and UK Point Absorber 44 m tall, 11 m diameter 8 km offshore 20 – 50 kW per unit Multiple units Commercial unit in Spain 1.39 MW
EnergeTech Australia Oscillating Water Column 35 meters wide 450 tons $2-3 Million Up to 50 meters offshore Double acting turbine
Fall ENERGY MANAGEMENTLecture Ideas for fuel-fired systems Almost two-thirds of the fossil-fuel energy consumed in the United States involves the use of a boiler, furnace, or other fired system. Over 68% of the electricity generated in the United States is produced through the combustion of coal, fuel oil, and natural gas. Boilers and fired systems or subsystems are not inherently energy efficientwith these systems there is significant opportunities for reducing energy consumption. Indeed, in operating the IAC for the first year, only 13% of the plants could have improved efficiency in their fossil- fuel fired systems but saved more than 80% of the energy recommendations (in MMBTU)
Fall ENERGY MANAGEMENTLecture Analysis of boilers and fired systems Governing equations –Not easybecause all values may change with time. Heat and mass balances are used to determine where all the heat or mass enters or leaves a system.
Fall ENERGY MANAGEMENTLecture Key elements for maximum efficiency Percent increase in efficiency or fuel savings = [(new eff.) – (old eff.)]/(new eff.) Ensure the furnace walls and stack vent are airtight and not a source of air infiltration. Ensure optimum burner performance Establish a maintenance program and establish an operators log and monitor key parameters. (Make corrections to operations if the key parameters change significantly.
Fall ENERGY MANAGEMENTLecture Exhaust Stack Temperature We need to reject stack gases at the lowest possible temperature consistent with design principles -- use additional heat recovery methods if the flue-gas temperature exceeds 250 o F. Excess heat can be recovered by adding an economizer to heat the the inlet (makeup) water should be T w = T g –100 o F or adding a gas/air pre- heater to heat the intake air. For units with stack gas in the >1,000 o F, use an additional unit to generate steam or other medium
Fall ENERGY MANAGEMENTLecture Requirements for maximum economy Boilers generally operate most efficiently at 65% to 85% full-load rating. Centrifugal fans (with motors) at 80% to 90%. Efficiencies fall off at higher or lower load points. It is usually more efficient to operate a lesser number of boilers at higher loads than larger number at low loads. Boilers should be put into service in order of decreasing efficiency starting with the most efficient unit. Newer units and units with higher capacity are generally more efficient than older, smaller units. Generally, steam plant load swings should be taken in the smallest and least efficient unit.
Fall ENERGY MANAGEMENTLecture Fuel Considerations Natural Gas: –Costs have been artificially low (up until recently) by government control. –Only limited equipment is necessary. –Boiler costs are less because of heat transfer and flame characteristics. –Little or no pollution control equipment is required. Fuel Oil: –Many classifications and makeup of oils –All fuel oil has a high heat value (HHV) and a low heat value (LHV). LHV is the heat produced during combustion but HHV is used in the US. –Viscosity can vary depending on the oil, the higher the viscosity the operation and design are more difficult. –Flash points are normally high, so fuel oils are relatively safe to handle. –Pour pointdetermines if storage heating is required in colder climates. –Sulfur content is an important consideration in meeting environmental regulations. –Ash and other contaminates can cause reduced heat transfer and lower efficiency. Coal: –Environmental limitations, higher capital costs, larger storage requirements, higher maintenance costs and increasing transportation costs.
Fall ENERGY MANAGEMENTLecture Steam and Condensate Systems Energy conservation opportunities: –General operations: Review operation of long steam lines Review operation of steams systems for occasional services. Implement regular steam leak survey. Monitor steam use. Reduce temperature requirements of heated storage vessels to the absolute minimum. –Steam trapping: Check sizing and institute regular survey and maintenance program. –Condensate recovery: Survey condensate sources presently discharged to waste drains Consider pressurizing atmospheric condensate to minimize flash losses.
Fall ENERGY MANAGEMENTLecture Continued Energy conservation opportunities (continued) –Mechanical drive turbines: Consider shutting down standby turbines. Clean turbines on a regular basis Consider CHP instead of large pressure-reducing valves. –Insulation: Use infrared thermography to locate areas insulation deterioration of piping and equipment on a regular basis. Re-evaluate insulating previously uninsulated equipment. Survey the economics of retrofitting additional insulation on insulated equipment.
Fall ENERGY MANAGEMENTLecture Steam properties and definitions British Thermal Unit (Btu)amount of heat required to raise 1 pound of water 1 degree Fahrenheit. Boiling pointthe temperature at which water begins to boil at any given pressure. Saturated and superheated steamsaturated temperature at a pressure will produce more steam and doesnt raise the temperature as more heat is added. If all water is boiled offand we continue to add heat and the temperature continues to rise this is called superheated steam.
Fall ENERGY MANAGEMENTLecture Boiler Blow down In steam generation using boilers, most water impurities are not evaporated with the steam and thus concentrate in the boiler water. The concentration of the impurities is usually regulated by the adjustment of the continuous blow down valve, which controls the amount of water (and impurities) purged from the steam drum. Too little blowdown, sludge deposits and carryover will result. Too much blowdown, excessive hot water is removed, resulting in increased boiler fuel requirements and inefficiencies.
Fall ENERGY MANAGEMENTLecture Energy Conservation Opportunities: General Operations: –Regular steam leak survey and repair. –Plant-wide steam balance to eliminate venting low- pressure steam Steam Trapping: –Regular survey and maintenance program. –Check sizing periodically. Insulation: –Survey and maintain on a regular basis –Review insulation economics of all uninsulated areas on a periodic basis.
Fall ENERGY MANAGEMENTLecture Definitions Sensible Heat –Heat input that can be sensed as in raising the temperature Latent Heat –Heat that goes into a process and converts it from liquid to vapor Enthalpy –Total energy content of a flowing medium (usually expressed in Btu/lb) takes both latent and sensible heat into account
Fall ENERGY MANAGEMENTLecture Steam Traps May represent a major energy conservation opportunity (or problem). Basic function of a steam trap is to allow condensate formed in the heating process to be drained from the the equipment. Inefficient condensate removal almost always increases the amount of energy required by the process and may produce water hammer (can cause equipment damage). Steam traps may also facilitate the removal of air from the steam space. The presence of air in the system reduces the temperature for heat transfer. Steam traps are sized in two specifications: condensate load (#/hr or gal/min) and the pressure differential across the trap (psig). It is a good idea to size the trap with a know load and a factor of safety (usually 3 or 4). Steam traps can either fail open (allowing live steam to discharge) or closed (causing condensate to back up into the steam systemmay lead to disastrous effects). Typically 15% to 60% of the traps in a system may be blowing through, wasting enormous amounts of steam and energy.
Fall ENERGY MANAGEMENTLecture HW 2Problems: 1-4 Due by 9/04/2012, 1pm At design parameters, what should be the O 2 content in the stack for a gas-fired boiler? All else being equal, what kind of combustion efficiency gains might be obtained by lowering the stack temperature rise from 450 o F to 250 o F? All else being equal, what kind of combustion efficiency gains might be obtained by lowering the stack O 2 content from 9% to 2%? Develop a spreadsheet that calculates boiler efficiency based upon stack temperature rise and O 2 content.
Fall ENERGY MANAGEMENTLecture HW2Problem 5 Setup a saving operation by running two boilers instead of three similar to that shown on pages : –Boiler 1: 140,000 #/hr., 186 BTU/hr. ? –Boiler 2: 140,000 #/hr., 204 BTU/hr. ? –Boiler 3: 70,000 #/hr., 100 BTU/hr. ?
Fall ENERGY MANAGEMENTLecture HW2Problem ft of 6-in. steam pipe carries saturated steam at 150 psig. Tables obtained from an insulation manufacturer indicate a heat loss from this piping run is presently 500,000 Btu/hr. With proper insulation, the manufacturers tables indicate that this loss could be reduced to 5000 Btu/hr. With the boiler at 85% efficiency, what is the steam savings and the fuel savings?
Fall ENERGY MANAGEMENTLecture HW2Problems 7, 8 Estimate the steam usage and fuel usage of a of a paper corrugator doing 100,000 ft 2 per hour. The efficiency of the current steam boiler is 75%. Estimate the steam usage and fuel usage of a 25 ft steam table in restaurant usage. The efficiency of the steam boiler is 80%
Fall ENERGY MANAGEMENTLecture HW2Problem 9, 10 What is the annual cost of a 1/16 inch diameter steam leak in a system operating at 250 psi with the normal cost of steam at $3.50/1000 lbs.? What things (and how) are to be inspected during routine maintenance of a steam system. Estimate potential savings by fixing suck things as traps and leaks.