We think you have liked this presentation. If you wish to download it, please recommend it to your friends in any social system. Share buttons are a little bit lower. Thank you!
Presentation is loading. Please wait.
Published byJoshua Lewey
Modified over 2 years ago
©Mammoth-WEBCO, Inc. 1 Mammoth Water-Source Heat Pumps
©Mammoth-WEBCO, Inc. 2 Introduction to Mammoth-WEBCO Began as Brown Sheet Iron and Steel Company manufacturing industrial gravity and forced-air furnaces 1953 – Acquired by private investors and renamed Mammoth Furnace Company and was the largest industrial furnace manufacturer 1965 – Acquired by Lear Siegler, Inc. and expanded into Heat Pump and Coil manufacturing 1986 – Acquired by Nortek, Inc. and joined their CES Group, Inc., largest group of custom HVAC manufacturers in North America 2009 – WEBCO, Inc. merged with Mammoth, Inc. to form Mammoth-WEBCO, Inc.
©Mammoth-WEBCO, Inc. 3 Youll Find Mammoth In Every Market Delivering custom-engineered air conditioning solutions Manufacturing Education Healthcare Offices Pharmaceutical High-Tech Food Processing Hotel/Motel Retail Amusement Government Hospitality
©Mammoth-WEBCO, Inc. 4 integrated Prefabricated Equipment Centers (iPEC) Custom chillers and chiller plants ULTRALINE packaged DX Roof-mounted air systems V-Cube floor-by-floor self- contained RMZ Vari-Zone Custom DX and multi-zone rooftop units And… We Continue to Grow Our Capabilities
©Mammoth-WEBCO, Inc. 5 Mammoth Water-Source Heat Pumps Water-source / Ground- source heat pump solutions Horizontal and vertical, indoor configurations Low-sound condominium unit
©Mammoth-WEBCO, Inc. 6 Holland, Michigan Plant New Factory Building - 45,000 Square Feet Manufactures All Water Source Products Manufacturing heat pumps for over 35 years
©Mammoth-WEBCO, Inc. 7 Small Single Circuit Horizontal And Vertical Units 10 different sizes from ¾ ton to 6 ton. N vintage equipment, available in standard and low (geothermal) temp applications. Horizontal units: Standard and mirror image, end discharge orientations available. Vertical Units: Right and left hand orientations.
©Mammoth-WEBCO, Inc. 8 Horizontal & Vertical Units General Galvanized G60 steel casing Access panels; compressor section, fan section and electrical box 2-sided filter bracket with 1" thick filter Threaded female NPT water connections Condensate drain connection Supply duct connection Fully insulated with 3/4", 1½ lb. coated fiberglass
©Mammoth-WEBCO, Inc. 9 Medium Horizontal Line 070H 6 ton 086H 7 ton 100H 8 ton 120H 10 ton 142H 12 ton
©Mammoth-WEBCO, Inc Medium Vertical Units 070V 6 ton 086V 7 ton 100V 8 ton 120V 10 ton 142V 12 ton
©Mammoth-WEBCO, Inc V-Cube Slim Large Vertical Units - 170V 14 ton 210V 17 ton 270V 22 ton 310V 25 ton 360V 30 ton 440V 37 ton 540V 49 ton
©Mammoth-WEBCO, Inc V-Cube Slim 14 through 49 Tons (Sizes ) Dual Scroll Compressor Units High EERs & COPs Quiet Operation Thermal Expansion Valves Heat Pumps (sizes ) or Cooling Only Optional VAV, Waterside Economizers, Hot Gas Reheat, DDC Controls, Double Wall, …
©Mammoth-WEBCO, Inc % Outside Air Units
©Mammoth-WEBCO, Inc % Outside Air Sizes Small Cabinet Size 071Nominal 6 tons Size 111Nominal 9 tons Size 141Nominal 12 tons Size 181Nominal 15 tons Large Cabinet Size 221 Nominal 19 tons Size 271 Nominal 23 tons Size 321 Nominal 28 tons Size 381 Nominal 32 tons
©Mammoth-WEBCO, Inc % Outside Air Unit Features Dual scroll compressors Thermal expansion valves Multi-blade low leak outside air damper with motor. 2" thick, 30% efficient pleated filters Additional 4 filters are optional Four-row evaporator coil ( six-row optional ) IAQ drain pan with side condensate drain connection. Hot gas reheat coil for dehumidification Hot gas by-pass Foil-faced foam insulation - no fiberglass. Belt drive fan assembly. Optional Mammoth MDDC controls.
©Mammoth-WEBCO, Inc Water-to-Water Units 1 thru 30 tons Includes: Compressor Source side HX Load side HX TX valve Unit can heat or cool water Part of the High Efficiency Unit Family
©Mammoth-WEBCO, Inc MCHH units Condo Heat Pumps Mechanical cooling, hot water heating. NC sound levels – 30 heating, 36 cooling. Designed for closet installation. Positive water shut off.
©Mammoth-WEBCO, Inc Whats Coming? U vintage single circuit 410A systems. M vintage twins & Quads 410A systems. E series large twin and quad circuits (410A). D vintage make up air units, (410A) indoor/outdoor applications. K vintage water to water units, 5 to 50 tons, (410A).
©Mammoth-WEBCO, Inc E Vintage Large Units Coming soon: stock cooling only, VFD, 410a refrigerant, double wall construction, fan wall design, pre-painted cabinet, ESP capability of up to 3, Mammoth DDC controls, Sizes available: 170 / 14 ton 210 / 17.5 ton 270 / 22 ton 310 / 25 ton 360 / 30 ton 440 / 40 ton 540 / 45 ton 620 / 52 ton 720 / 60 ton
20 ©Mammoth-WEBCO, Inc. Control Options
©Mammoth-WEBCO, Inc HP-4 Microprocessor Incorporated in all Mammoth heat pumps. High & low voltage protection. Random start time delay from 5 to 35 seconds. Compressor anti-short cycle protection (5min.) Electronic condensate alarm. Compressor lock out with auto reset. Fan interlock, with compressor operation. Emergency shut down / field supplied signal. Dry contacts for fault indication to DDC control. Aux contacts with compressor operation. Test pin jumper / disables timing circuits for testing. LED fault identification / status indication Removable terminal strip for thermostat wire connections.
©Mammoth-WEBCO, Inc HP-4 Microprocessor Room temperature control Can be used with any HEAT PUMP T-stat. Mammoth heat pumps fail to heat (RV) energized for cooling (O) terminal. LED unit status codes: on steady = Normal operating mode 1 flash = High or low pressure trip. 2 flashes = Emergency shut down (by others) 3 flashes = Auxiliary switch fault. 4 flashes = Condensate alarm 5 flashes = Low voltage fault 6 flashes = High voltage fault 4 tries on auto re-set in 6000 seconds (1.6 hrs) Lock out occurs, and must be re-set manually. (remove call for compressor at t-stat or cycle power to unit)
©Mammoth-WEBCO, Inc HP-4 Microprocessor Typical Wiring P1 terminal block (t-stat wiring) P1-8 lock out alarm out put P1-7 Call for compressor Y P1-6 NSB signal P1-5 Supply Fan G P1-4 24VAC (-) P1-3 24VAC (-) O P1-2 2 hr override P1-1 24VAC (+) R
©Mammoth-WEBCO, Inc HP-4 Microprocessor Typical Wiring Other contact points / P2 terminal strip P2-8 A.D. Contacts (NC) P2-7 A.D. Contacts (com) P2-6 A.D. Contacts (NO) P2-5 Unoccupied Input P2-4 Emergency Shutdown P VAC (-) P2-2 Dry Contacts Alarm P2-1 Dry Contacts Alarm
©Mammoth-WEBCO, Inc Mammoth DDC controls I/O Zone 560 Space temperature control 5 digital Outputs, 6 universal inputs. 100% stand alone control. Capable of communication: via BACnet, Modbus, N2, Lon talk. Includes communication with intelligent space sensors, and keypad/display units. For use with standard CAV heat pumps without water side economizers or hot gas re-heat. Orders must include minimum of one key pad per order.
©Mammoth-WEBCO, Inc Supply air temp / monitor only Water HX LWT Water HX EWT (thermistor/dry contact) net work Comp Lckt / overflow, compr#1 HP-4 alarm, comp#2 alarm Load shed, Comp#1Q* HP4 alarm Comp#2Q* HP4 alarm Emergency shut down, External start, dirty filter* Typical Wiring
©Mammoth-WEBCO, Inc Rnet Room/return air Temperature (RS Std) Or RS Pro Fan start Call for #1 comp Call for #2 comp. Reversing valve Common alarm Typical Wiring
©Mammoth-WEBCO, Inc Mammoth DDC controls I/O Zone 583 Space temperature control 5 digital outputs, 8 universal inputs. 3 analog outputs 100% stand alone control. Capable of communication: via BACnet, Modbus, N2, Lon talk. Includes communication with intelligent space sensors, and keypad/display units. For use with standard CAV heat pumps with water side economizers or hot gas re-heat. Orders must include minimum of one key pad per order.
©Mammoth-WEBCO, Inc I/O Zone 583 Typical wiring the same as 560 except 583 has three analog outputs Analog outputs require DC relay for single stage, USC for multi stage or actuator for modulation of control Outputs normally used for re-heat, 3ater side economizers or aux heat Used for CAV with de-humidification and hot gas re-heat. Also special applications with water to water units.
©Mammoth-WEBCO, Inc & 583 Control Interface Room temperature control RS Plus offers a local setpoint adjustment and override to an occupied mode and LED indication of current status. RS Pro offer the same and a large LCD display. Both sensors provide precision temperature measurement, communication capabilities, able to mate up with key pad for commissioning and maintenance. RS Plus RS Pro
©Mammoth-WEBCO, Inc I/O Flex 6126 Discharge air controller 6 digital outputs, rated at 5 250VAC. 12 universal inputs, configurable for dry contact, thermistor/RTD, 0 to 20ma, 0-10 VDC. 6 analog outputs, 1&2 are 0-10 VDC or 0-20ma, outputs 3 through 6 are 0-10 VDC only. Used in large twin, make up air units, primary use for units that have modulation control of heat source or control of VFD,
32 ©Mammoth-WEBCO, Inc. WSHP Job References
©Mammoth-WEBCO, Inc Pacific Bell Park Location: San Francisco, CA A wide range of units were installed throughout the park. They include small horizontal heat pumps, twin circuit verticals, V- Cube Lites, and V-Cubes Mammoth worked with the developer to provide special arrangements and performance that better suited the layout of the park.
©Mammoth-WEBCO, Inc Viacom Location: New York, NY Viacom selected V-Cubes and horizontal heat pumps that worked with their open and closed ceilings. Quick delivery was a key point for many units. Some units utilize DDC controls and VAV to service the studio and larger areas of the building.
©Mammoth-WEBCO, Inc Quality Living Assisted Care Facility Location: Omaha, Nebraska Quality Living added a new east campus to their facility. The new campus utilized Mammoth high efficiency geothermal heat pumps. The new addition operates more than twice total hours at less cost than the older campus with a conventional boiler and tower system.
©Mammoth-WEBCO, Inc Texas Motor Speedway Condominiums Fort Worth, TX Mammoth was awarded the project because of energy savings, noise control, flexibility in right/left hand configuration and meeting the tight closet fit.
©Mammoth-WEBCO, Inc Sherman Hospital, 255 bed Location: Chicago, IL Worlds Largest Geothermal Hospital Over $1.0 Million energy savings annually 732 Mammoth Water-to-Air Terminal Units 18 Governair RSA Air Handlers with Vestibules & Governair controls
©Mammoth-WEBCO, Inc Mammoth Water-Source Heat Pumps How can we help you today?
SMALL SINGLE CIRCUIT HORIZONTAL AND VERTICAL UNITS ½ ton to 5 ton.
3.2 What principles are used to vary the amount of HVAC service to a space with varying loads? Chapter 3. HVAC Delivery Systems 1) Constant-Temperature,
Spec Stoppers Sweet Spots Specials 1. How To Make $6,000 MORE on a 26 ton Data Aire Series DX Unit 2.
ACTIVE LEARNING PROCESS Prepared By : Dishant Panchal 13BECEG112 Neeshit Kaushik 13BECEG122 Neel Panchal 13BECEG116 Guided By : Prof. Jugal Panchal Branch:
Packaged Rooftop Air Conditioning Unit Presents the.
HEAT PUMPS CPLE Heat Pump CPLE 10 S.E.E.R. Low pressure control Accumulator Check-flow rater expansion device Defrost controls.
PSSA Preparation. Question 1(no calculator) D Question 2 (no calculator)
Siemens Building TechnologiesRWD heatpump controllers Xavier Zabalegui/David Jefferson 1 January 2003 RWD Heat Pump controllers RWD Heat Pump Controllers.
2 Maxinet is a web based, Mini BMS application for controlling Central HVAC System. It enables a secured monitoring & control of the HVAC system at site.
Visit us at MCS’S MAGNUM DIAGNOSTICS PACKAGE MICRO CONTROL SYSTEMS ONLINE TRAINING FACILITY.
Engineered Products Make-Up Air for Heating and Cooling.
Time for a BREAK! You have 45 Minutes. Time Left 44.
Roof Top Unit Overview (MAGNUM) Visit us at Revision- 12/17/2015.
Page 1 Peng Xu, Philip Haves, James Braun, MaryAnn Piette January 23, 2004 Sponsored by the California Energy Commission and the California Institute for.
Engineer Presentation. Efficiency - GAS Clamshell Heat Exchanger 80% Efficient.
Environmental Controls I/IG Lecture 14 Mechanical System Space Requirements Mechanical System Exchange Loops HVAC Systems Lecture 14 Mechanical System.
Aqualean Product Presentation 1 By Laurent Domenget Product Manager, Rooftop & Packaged Air Units.
Rev. Sept. 18, Electrical Power S64F Model Helicopter.
Tom Johanson – DNV KEMA Senior Engineer Building Automation Systems.
HVAC 101 The Basics of Heating, Ventilation and Air Conditioning Presented by: Mike Barcik and Jeff Ross-Bain, PE Southface Energy Institute.
HVACR416 - Design Air Handler Terminology. Basic System Components Condenser o Condenser Coils o Compressor o Condenser Fan.
Click left mouse button to advance, back to return Refrigeration HVAC control & monitor system Presscon Network & Pressnet Software Click left mouse button.
Visit us at MicroMag Control System.
Introduction to Energy Management. Week/Lesson 13 Control Strategies for Occupant Comfort.
HVAC Basics Bin Yan HVAC – Heating, Ventilation, Air-conditioning.
© 2004 Venmar CES Inc.© 2006 CES Group - Confidential 1 Mammoth Product Training Chiller Systems.
Trane Voyager rooftop units Trane Voyager rooftop units combine heating, cooling, and fan sections all in one for simplified application and installation.
BMU - E I 1 Development of renewable energy sources in Germany in
Zone Control Air System Why? 1.Provides room by room comfort control. 2.Reduces equipment run time. 3.Eliminates hot/cold rooms. 4.Works with conventional.
MCS LWC MAGNUM ORIGINAL CONCEPTS Designed to Control Loop Systems Build to be generic and handle many configurations of Loop Controllers Type of.
C Copyright © 2005, Oracle. All rights reserved. Practice Solutions.
AC-SSC-1 Installation and operation manual. The SpacePak AC-SSC-1 is an interface module that allows communication between a wide variety of commercially.
Lindbergh Field International Airport New Terminal Bill Mahoney LSW Engineers.
John Ogilvie High School - CfE Physics 1 CfE Physics – SCN 4-09 b & c Electronics Input, Process and Output Digital Logic Gates SCN 4-09b: By contributing.
UCSD Medical Center - Hillcrest Campus Case Study Gerry White Facilities Design & Construction University of California, San Diego.
ELECTROLUX REFRIGERATOR Control Board TURN TO PAGE 183 IN YOUR TRAINING MANUAL.
A process in which one event follows another until a job is completed Event 1Event 2Event N For a process with N steps …….. Characteristics 1.) Discrete.
1 Series V4T 1/4 DIN Temperature Controllers. 2 3 Watlows Next Generation Styling Series 97 Matching 1/16 DIN Limit Controller Series F4S and F4D Ramping.
FIGURE 7.1 Elements of the final control operation. Curtis Johnson Process Control Instrumentation Technology, 8e] Copyright ©2006 by Pearson Education,
BMU – KI III 1 Development of renewable energy sources in Germany in
Relay Control Programming Basics Offsets and Differentials, 2 Setpoints.
CON 4003 Construction Estimating Prof R. V. Locurcio.
Copyright © 2012, Elsevier Inc. All rights Reserved. 1 Chapter 7 Modeling Structure with Blocks.
PP Test Review Sections 6-1 to 6-6 Mrs. Rivas 1. 2.
Sustainable School Design Creating Healthy, High Performance School Facilities Presented by Stephen M. Koontz, Energy Services Leader, Tampa Bay Trane.
1 BACKGROUND ALARM SYSTEM OF ZXJ10 Training Center Zhongxing Telecom Pakistan (Pvt.) Ltd.
1 Packaged HVAC Equipment. 2 Is the most common source for HVAC in small to medium commercial buildings Is the most common source for HVAC in small to.
SECTION 7 AIR CONDITIONING (COOLING) UNIT 38 INSTALLATION.
© 2017 SlidePlayer.com Inc. All rights reserved.