Download presentation

Presentation is loading. Please wait.

Published byMaci Crowe Modified over 2 years ago

1
COMPARATIVE ANALYSIS BETWEEN SUPERMARKET FREEZER WITH REMOTE COMPRESSOR AND PLUGIN FREEZERS WITH BUILT IN COMPRESSOR Nelson de Jesus – Technical Department

2
Layout With Plug-in Cabinets Nelson de Jesus – Technical Department Fricon Equipments to use: 12x SMR 2200SL Net Volume: 584dm3 Ocupied Area: 1,914 m2 Consumption in 24h: AD model: 11,6KWh/24h Variable Speed: 6,2KWh/24H 4x SMR 1700SL Net Volume: 450dm3 Ocupied Area: 1,479 m2 Consumption in 24h: AD model: 9,2KWh/24h Variable Speed: 5,1KWh/24H 4x SMR 1900SL Net Volume: 480dm3 Ocupied Area: 1,653 m2 Consumption in 24h: AD model: 8,3KWh/24h Variable Speed: 5,1KWh/24H

3
Nelson de Jesus – Technical Department Totals for the 2 Plug- in Islands

4
Layout With Remote Compressor Islands Nelson de Jesus – Technical Department Equipments with Remote Compressor: 4x Cosmo 3 LG300:2500 Net Volume: 1610dm3 Ocupied Area: 5,04 m2 Consumption in 24h:15,51KWh/24h 2x Cosmo 3 LG300:1880 Net Volume: 1214dm3 Ocupied Area: 3,79 m2 Consumption in 24h:10,62KWh/24h 4x Cosmo 3 TG300 Net Volume: 640dm3 Ocupied Area: 2,16 m2 Consumption in 24h:10,62KWh/24h The consumption indicated are only for the peripherals of the cabinets: fans, defrost resistances, glass resistances

5
Nelson de Jesus – Technical Department Totals for the 2 Remote Compressor Islands

6
Nelson de Jesus – Technical Department Totals for the 2 Remote Compressor Islands Cabinet Peripherals: Evaporator Ventilator - 80W; Drain Resistance – 289W; Evaporator Resistance – 1980W; Recory Resistance – 1050W; Tray Resistance – 78W; Glass Resistance – 80W. Compressor : Brand– Bitzer; Reference – 4NC 12.2Y; Gás – R404a; Cooling – 8920W Power Consumption – 14.1KW; Peak Current – 69A

7
Nelson de Jesus – Technical Department Consumption per Liter Comparison

8
Year Consumption Comparison Nelson de Jesus – Technical Department

Similar presentations

© 2016 SlidePlayer.com Inc.

All rights reserved.

Ads by Google