Presentation on theme: "Incident took place at OPP substation at 9. 31"— Presentation transcript:
1Incident took place at OPP substation at 9. 31 Incident took place at OPP substation at hrs on the 13th of Feb 2007.Six persons were injured (4 from OPP and 2 from EPC contractor)One person died at Sohar hospital later in the day6.6 KV switchgear (incomer to Main Transformer ‘B’) was damaged in the incident
2Emergency Response Team responded immediately and conducted a search and rescue operation Incident declared as level 2ROP Civil defense and SRC called immediately and they arrived at 10 a.m.Site declared normal at hrs
3Summary of the incident On 09:31:38 13th February 2007, ground fault through the human occurred during rectification work on the earth switch inside the voltage transformer compartment of the 6.6 KV incomer ’B’The technicians have isolated the Circuit breaker of the 6.6kV Incomer B (secondary of the main ‘B’ transformer) and then tried the earth switch which did not close.Then they opened the 6.6kV voltage transformer cabinet door overlooking the isolation of 33KV primary of the transformer.After racking out the Voltage Transformer, the person approached inside the cabinet compartment of incomer B to rectify the Earth Switch mechanism while the bus was live and the accident took place.
4Single line diagram of Incoming power CB (0BF1)TR1BVTES6.6KVFEEDER CBTIE CB (0T)CB (0AF1)CB (1A)TR1A33 KVTIE CB (1T)33KV FROM SRC SUBSTATIONINCIDENT LOCATIONCB (0B)CB (0A)CB (1B)33 KV primary not isolated6.6KV incomer
9Root Causes for the accident Transformer primary 33KV power supply not isolated hence 6.6 KV incomer to the switch gear was live.Opening of 6.6 KV switch gear bottom voltage transformer door and removal of transformer and side cover to rectify earth switch without valid work permit and under live conditions.
10Causes contributing to the accident Isolation of 33 KV primary supply to transformer ‘B’ which was mentioned in the work permit was not accomplished and Earth switch for 6.6 KV incomer switch gear not working.Logic provided by ABB vendor in the 6.6 KV incomer ‘B’ earth switch was incorrect and not matching with construction drawings. This incorrect logic was also preventing the earth switch from closing. (Post observation)Maintenance procedure was not followed strictly.Opening the Voltage Transformer door, removal of Voltage transformer and rectifying the earth switch without hazard analysis and work permit.Assumption that primary has been isolated and Misconcept that breaker cabinets for motor and incomers are same.Inadequate supervision and control of the job.
11Recommendations Permits to work system to be followed strictly. Tool box talk to be carried out before starting the job.Problem analysis to be done before performing rectification work.Logic design provided by ABB to be reviewed and rectified.Maintenance procedure to be followed strictly.Implement access control on the bus / voltage transformer doors when it is in live condition.Instructions on the secondary and incomer primary breakers that isolation else where is required for power OFF.Use of High voltage tester before accessing bus related work.Additional training for electrical team on ABB switchgears.Implement additional control measures for performing work on High voltage systems.