We think you have liked this presentation. If you wish to download it, please recommend it to your friends in any social system. Share buttons are a little bit lower. Thank you!
Presentation is loading. Please wait.
Published byDuane Walder
Modified over 2 years ago
BY PHIL RODIN Air and Water Chiller Basic Class
Things to check when chiller is not running or is in alarm
Alarm showing water flow, pumps both chilled and condenser water types of flow switches
Alarm showing water flow, pumps both chilled and condenser water types of paddle switches
Alarm showing water flow, pumps both chilled and condenser water types of electronic flow switches Electronic flow switches have probes
Alarm Conditions High Pressure 1. Low water flow 2. Cooling tower 3. Strainers (locations?) 4. Valves (electric or manual types) 5. The entering and leaving water temp. 6. Approach temp
Alarm conditions Chilled water flow 1. Pumps 2. Strainers 3. Valves (manual and electric) 4. Flow switches 5. Water temp in and out 6. Approach temp
Alarm conditions Chilled water flow (cont.) PRV
What is the oil temperature? 1. Feel the tank or read with inferred. 2. Check control panel 3. Check for power 4. Think out of the box, How can we heat this?
What is the oil temperature? (cont.)
Pressure & Temp. Gauges (electronic)
Pressure & Temp. Gauges (fluid type)
Chiller Surging ASK YOURSELF????? 1. Is it a high or low end surge? 2. Are your amps going up or down? 3. The sound? a. Is it an elephant b. Is it a grumble
Chiller Surging (High & Low Surging) High Surge on Low Pressure Machines 1. Water temp. in and out. 2. Approach 3. Cooling Tower 4. Purge 5. Refrigerant levels
Chiller Surging (High & Low Surging)
Chiller Surging (capacity control)
Chiller Capacity Control
Low End Surge 1. Water temp. In and out 2. Approach Temp. 3. Water pressure 4. Refrigerant levels
Low End Surge
Transducers & Sensors Types
Panel Codes 1. Carrier code 1111 2. York code 9675 aka YORK 3. Trane code ++--++ (different combinations)
Hows the Chiller Running? Is the chiller running in local? Is the chiller running in EMS? Are the pumps running? Are the valves open? Hand –off Auto (Think before going to hand)
Cavitation of Pumps 1. Strainers 2. Water pressures 3. Couplings 4. Valves 5. Primary or Secondary Loop
Questions (There is no such thing as a dumb question) ?
Chiller basics With Phil Rodin. Things to check when chiller is not running or is in alarm.
1600 Series Operation (See Installation and Operation Manual for detailed instructions)
Ventricle Chamber Valve Imaging Chamber ECG Machine Aortic Compliance Chamber Buffer Chamber Secondary Compliance Chamber Flow Meter Pressure Sensors DAQ.
Engine Speed Amps Engine Temp. Engine Oil Pr. Trans. Fluid Pr. Battery overheat Engine overheat Exhaust hose overheatExhaust overheat Low oil pressure.
INTRODUCTION. Function of Chillers Remove Cool Control Support.
Heat and cold generation Meyer Hospital Florence Meeting, 8-9 May 2003.
Pool system components - solar collectors - Temperature probes relief pool - Solar pump system - Pump filtration system - Relief valve - air temperature.
Claudio Bortolin. 1 st June: PT100 electrical connection failure (Temp Chiller water In&Out) 1) it required an access to the cavern to be fixed 2) access.
Perform Control Test. Check for Consistent Liquid Temperatures Entering and Leaving Liquid Temperatures should be close when the water pumps are on but.
A Trane Air Conditioning Clinic Centrifugal Water Chillers Air Conditioning Clinic TRG-TRC010-EN © American Standard Inc
Left side compressor behind Left control box Right side compressor behind Right control box.
ME444 ENGINEERING PIPING SYSTEM DESIGN CHAPTER 10 : CONTROL VALVES IN CLOSED LOOP SYSTEMS.
WELCOME. Glycol Refrigeration A most basic definition of refrigeration is taking heat from someplace we don’t want it and moving it to someplace where.
Daikin Altherma™ Troubling Shooting. 2 Code: 81 Part: Outlet water thermistor Location: Activation failure: Possible action to resolve the problem: –Check.
General Troubleshooting Tips. Troubleshooting General Troubleshooting Tips 1.This program is not intended to cover troubleshooting of all the components.
Flooded Screw Chiller FWSF Electronic Expansion Valve Condenser Evaporator Control box compressor Flooded Screw Chiller - FWSF.
Air conditioning – Refreshes your life Mini-Chiller Applied Systems Sales1 EWA(Y)Q-AAV3P Residential Mini-Chiller Heating EWAQ - AA3VP EWYQ - AAV3P Cooling.
James McIntyre VRF Training Manager V5 Key Components.
For internal use only — Carrier confidential Phase 1 - ABC’s of Comfort - Psychrometrics Level 1 - Load Estimating Level 2 - Principles of Mechanical Refrigeration.
Rack Refrigeration Systems ©2015 Master-Bilt Products, an unincorporated division of Standex International Corporation. All rights reserved.
Lecture Objectives: Cooling towers and modeling Project 1 Thermal storage systems.
Water Handling Operations Unit 4C - Foam and Foam Proportioning Equipment 4C-1.
Thermosyphon - Free Cooling Smardt Chiller with Thermosyphon.
Air Valve Switch System Upgrade for MACI 2500L Fire Truck Current system Operation (Structural) The current valves operate when is applied to one side.
MILK PASTEURIZER. One milk pasteuriser with a capacity of litres of milk for hours, HTST type with an operate range from 75° to 95°C, including.
Claudio Bortolin 03/09/2012. SPD (RP analyses required) 1) Pump 17b replacement and leak test 2)Pressure test on the old inlet lines (technicians coming.
Refrigeration What's Refrigerated? What makes up a system?
Install new air cooled high efficiency screw chiller (variable speed) Install new fan coils with ECM motors and low temperature heating coils and proper.
Purgers and Non-condensables “What are they and why should I care?” Refrigerating Specialties Division Parker Hannifin Corporation July 2004.
HYDRONIC HEATING AQUASTATS. I. TERMS A. HYDRONIC A. HYDRONIC 1. SYSTEMS THAT USE THE CIRCULATION OF HOT WATER THROUGH PIPES TO HEAT CONDITIONED SPACE.
BROAD Absorption Chiller Working Principle and Central A/C System Lecturer-Bob.
Section 703 Apparatus Inspection. Procedures The driver/operator should follow a systematic procedure for inspecting apparatus This ensures that all important.
TECHNICAL TRAINING Mini Chiller Panel Controller V2.0.
1 Summer Training On Refrigeration and Air Conditioning From:-Amber Enterprises PVT.LTD.
Series Operational Training. 2 Water Tank Water Pump Multiple Discharges 2000 Series Line Strainer Foam Tank Electronic Direct Injection Proportioner.
PowerPoint ® Presentation Chapter 6 Refrigeration Systems Refrigeration Mechanical Compression Refrigeration Absorption Systems Troubleshooting and Maintaining.
Heating Systems HVAC 11a CNST 305 Environmental Systems 1 Dr. Berryman 11aHeating Systems; Fuels; Boilers; Furnaces; Hydronics, Radiant Heat Chapter 5.
JOHNSON CONTROLS DAMPERS VALVE ACTUATORS BAS JOHNSON CONTROLS ROOM TEMP SENSORS.
1B-1 Fire Engine Maintenance Unit 1B – Pump Inspections and Maintenance.
MICE Hydrogen Control System MICE Safety Review Meeting 4 th Oct 2011 PJ Warburton - Daresbury Lab.
CAFS On-Line Orientation Montgomery County Fire & Rescue Service Making CAFS.
1 Piping Systems. 2 SERIES LOOP MONOFLO SYSTEM DIRECT RETURN REVERSE RETURN PRIMARY/SECONDARY SYSTEM BASIC PRIMARY SYSTEM SYSTEM SYZER.
Engineer Training Pneumatic System Overview. Engineer Training Confidential 2 Working Concept Overview: The Pneumatic System is comprised of: Y Pistons.
Service Section Technical Training December 2005.
1 LBT Q Engineering Review PLMG: Plumbing, includes IC system, chiller systems, instrument lab cooling, and LUCIFER cryo-compressor cooling.
Johnson Controls1 Heat Pump Jean-Pierre Perron Sales Executive Johnson Controls,division YORK 0499/
Filter manifold Holding tank Iron- manganese filter Aeration tank Control unit Pre- filter To storage tanks Backwash overflow SO2 vent Bypass Cutoff valve.
How Refrigerators and Freezers Work A refrigerator is a machine that can make its inside colder A refrigerator is also called a “fridge”
1. - Condensate pump and feed pump trip! -Turbine trips! 2.
CPPM Pixel Evaporative Cooling Plant Description & Operation with C 3 F 8 or C 4 F 10 G. Hallewell, CPPM, Feb 07, 2005.
© 2017 SlidePlayer.com Inc. All rights reserved.