2 Suite of HW products Tecomat Foxtrot Important features: High performance Modularity Installation module circuit-breaker design Two-wire free I/O topology Connectivity of CIB components Number of I/O up to I/O CIB elements Ethernet, Web server On-line programming SW backup OPC server Slot for MMC card for secondary memory MODBUS, PROFIBUS DP, CAN Tecomat Foxtrot – small powerful modular PLC system for a wide range of small-size to medium-size applications in industry and building. Inels – intelligent electrical system for building applications using CIB bus.
3 Tecomat Foxtrot – description
4 Tecomat Foxtrot – modules
5 Tecomat Foxtrot – communication Ethernet
6 Tecomat Foxtrot – Communication modes Channel CH1 Mode PC- communication with superior systems through the EPSNET protocol Mode PLC- data sharing among PLCs in the EPSNET-F network Mode UNI- common channel with arbitrary asynchronous communication Mode MPC- data exchange with subordinated PLCs in the EPSNET multimaster network Mode MDB- communication with superior systems through the MODBUS protocol Mode PFB- master for the connection of stations PROFIBUS DP slave Channel CH2 Mode PC- communication with superior systems through the EPSNET protocol Mode PLC- data sharing among PLCs in the EPSNET-F network Mode UNI- common channel with arbitrary asynchronous communication Mode MPC- data exchange with subordinated PLCs in the EPSNET multimaster network Mode MDB- communication with superior systems through the MODBUS protocol Mode PFB- master for the connection of stations PROFIBUS DP slave Mode UPD- operation of special submodules Mode DPS- realization of station PROFIBUS DP slave Mode CAN- connection of stations on the CANopen bus Mode CAS- realization of station CANopen Mode CAB- connection of the CAN bus Mode CSJ-connection of CAN interface with SJA1000 driver Ethernet ETH1 Mode PC- communication with superior systems through the EPSNET UDP protocol in TCP/IP networks Mode PLC- data sharing among the PLCs in the TCP/IP network
7 Tecomat Foxtrot – controlling with I/O Energy monitoring Direct controlling energy sources and consumption (IRC systems] Process optimization. All standard PLC functions, fast inputs for counters, incremental position encoders, measurement of pulse length, period and phase shift.
8 What is an intelligent electro installation system? System of sensors and actuators which are situated on one bus and connected to control system. They work as remote I/O.
9 FOXTROT = communication + I/O Communication part – at the left part –Ethernet 10/100 (RJ45) –CH1-RS232 UART up to 340kbit/s –CH2 – optional for 1 submodule –RS232 - MR0104 –RS482 –RS422 –1xCAN –2xCAN –Profibus DP slave –…LON atd. –Expansion by peripherals I/O modules - Bus TCL2 –Expansion INELS - Installation elements –Power supplying 24V/DC Ethernet 10/100baseTX UTP RS232 Optional interface/ for submodule MR TCL2 INELS 24V DC
10 FOXTROT = communication + I/O CP-1004 Basic I/O – at the right –INPUTS - basic functions 8x DI 24V DC (DI0-DI7) –INPUTS - alternative functions DI4-DI7 = analog AI0-AI3 –0-10V –10bit, –bez GO DI0-DI3 = special functions FI0-FI3 –Fast counter, –Incremental sensor –OUTPUTS 6x DO/RO, –Switching /NO/ contact relay –230V AC/3A Optical indication DI0……………..….DI7 AI0…AI3FI0..FI3 RO0………………RO5
11 FOXTROT = basic types of I/O DI4……………..….DI11 DI0….DI3 SPI0..SPI3 IB DI 0 AI 0 AO 0 RO 3M RO0………………RO7 DI0….DI3 FI0..FI3 IR DI/FI 0 AI 0 AO 8 RO 3M AI0……………..AI7 A00…A01 Vref IT DI 8 AI 2 AO 0 RO 3M DO4……………DO11 DO0..DO3 0S DI 0 AI 0 AO 12 DO 3M RO0………………RO5 DI0……………..….DI7 AI0…AI3FI0..FI3 CP DI/FI 4 DI/AI 0 AO 6 RO 6M
12 FOXTROT – modularity, connection 24V DC Module address 0-9 System bus –345kbit/s –BUS/RS485 – m –Terminator is required –Basic module has to be at the left Power supplying 24VDC Up to 300m
13 Bus installation units for the CIB bus Individual work with remote I/O Free topology – two wires Mosaic libraries of function blocks for simple building installations –heating (air conditioning, ventilation), –illumination (dimming, time functions), –electronic alarm system functions –dim-out control, –… For sophisticated technological applications in the field of building, source and heat distribution control.
14 FOXTROT is expandable by CIB elements 24V DC CIB –Data + Power supplying –2 wires –Free topology –24V DC –32 units CIB MASTER –Next 2 buses –2x32 units CIB is suitable for building IRC (Individual room control) –Lighting –Heating –Air-conditioning –Alarm system –…–… 230V AC CIB
15 FOXTROT – Expansion of CIB buses Power 230V AC/ 27.2V DC CIB -1 CIB-2 CIB-3 CIB-4 CIB-5 CIB-6 CIB-7 CIB-8 CIB-9 9 x 32units = 288 units 288 x 14DI = 4032 DI = max.
16 24V DC SELV 230V AC CIB works with safety voltage SELV Power 230V AC/ 27.2V DC CIB kV
17 Building Management System TECOMAT FOXTROT + CIB/INELS For control panels Room installation Interiercomponents Acces control Security CCTV Video INTEGRATION DIRECT CONTROL EthernetRS485 Electricity supply DDC/PLC Cooling DDC/PLC Heating DDC/PLC Intelligent Installation Fire signalization
18 Web server & client, File server Embedded web server Embedded web server It uses XML, which is more structured than HTML and doesn't spend the capacity of CPU. It uses XML, which is more structured than HTML and doesn't spend the capacity of CPU. Foxtrot uses file system on Flash disc, internal or on MMC/SD card Foxtrot uses file system on Flash disc, internal or on MMC/SD card Limitation is only the size of MMC/SD card
19 INELS BUS DI (DI), DO/ROAIAOSpecial Elements to installation box External Temperatur e sensor 8x DI IM2-80B 1x DI, 1x DO 1x RO 2x RO LM2-11B SA2-01B SA2-02B 4x 0-10V DAC2-04B/0 4x 1-10V DAC2-04B/1 2x dimming LM2-22B DIN rail modules 1M, 3M - 14x DI IM2-140M 2x DI, 2x DO 2x RO 4x RO DA2-22M SA2-02M SA2-04M 4x 0-10V DAC2-04M/0 4x 1-10V DAC2-04M/1 2x dimming LBC2-02M Elements for interiors ELEGANT Internal Temperatur e sensor 2 buttons 4 buttons 8 buttons Analog/Digital WSB2-20 WSB2-40 WSB2-80 thermostats IART2 SOPHY SOPHY L CIB Units - overviewVoice Light Infra Button Infra