Measure Summary Retrofitting insulated glass doors to existing medium temperature open multi-deck cases Provisional savings estimates ~440-kWh/lin ft and 52-therms/lin ft Based on a DOE2.2r simulation Requesting Provisional UES Status 3
Proposed Provisional UES Values Measure Site Savings (kWh/ft) Site Savings (therms/ft) Measure Life Capital Cost ($/ft) TRC B/C Ratio Door Retrofit- No night covers in Baseline/Multiplex Compressor- Seattle, WA457.257.412$566 1.9 Door Retrofit- Night covers in Baseline/Multiplex Compressor- Seattle, WA415.251.912$566 1.8 Door Retrofit- No night covers in Baseline/Stand-alone Compressor- Seattle, WA477.457.412$566 2.0 Door Retrofit- Night covers in Baseline/Stand-alone Compressor- Seattle, WA432.751.912$566 1.8 Door Retrofit- No night covers in Baseline/Multiplex Compressor- Spokane, WA419.151.712$566 1.8 Door Retrofit- Night covers in Baseline/Multiplex Compressor- Spokane, WA377.546.512$566 1.6 Door Retrofit- No night covers in Baseline/Stand-alone Compressor- Spokane, WA436.751.712$566 1.8 Door Retrofit- Night covers in Baseline/Stand-alone Compressor- Spokane, WA392.746.512$566 1.6 Door Retrofit- No night covers in Baseline/Multiplex Compressor- Billings, MT417.348.012$566 1.7 Door Retrofit- Night covers in Baseline/Multiplex Compressor- Billings, MT371.643.112$566 1.5 Door Retrofit- No night covers in Baseline/Stand-alone Compressor- Billings, MT433.948.012$566 1.8 Door Retrofit- Night covers in Baseline/Stand-alone Compressor- Billings, MT386.143.112$566 1.6
Standard Protocol Checklist 5 Link: Appendix A - Guidelines Checklist Grocery Refrigeration Systems.xlsx Appendix A - Guidelines Checklist Grocery Refrigeration Systems.xlsx
Modeling Methodology 6 Modeled using DOE 2.2R Typical store was built using GrocerSmart Audit Data Multiplex Baseline assumes Floating Head Pressure, T8 lamps, and EC motors are in place. Stand-alone system baseline assumes T8 lamps and EC motors. Infiltration, conduction, and radiation load based on manufacturer data, the ASHRAE Refrigeration Handbook, and SCE lab test reports
Calibration Plan Collect Metered Data – Rack: Volts, Amps, PF – Condenser: Volts, Amps, PF – HVAC Unit: 1-time Voltage reading, Amps – Hourly Natural Gas via Utility Interval Meter – Hourly Outside Air Temperature Minimum 3 weeks baseline Minimum 3-weeks post – This is a direct load measure. We expect less seasonal interaction than system measures like floating head pressure. 12
Calibration Plan Develop regressions for daily or hourly refrigeration use correlated to ambient temperature Annualize using TMY data – Pre, Post and Savings (Pre minus Post) 13
Calibration Plan Collect DOE2.2r inputs per data collection specifications Use inputs to run DOE2.2r for Baseline & Post estimates of total refrigeration energy Compare estimates of Baseline, Post & Savings estimates of refrigeration energy to best-practice estimates Modify DOE2.2r models and iterate tests until both baseline energy use, post energy use and energy savings at all sites are reasonable and there is no significant bias. 14
RTF Proposed Motion: I _________ move that the RTF approve the UES for Adding Doors to Open Multi-deck Cases under provisional status and place the measure Grocery-Night Covers Under Review.
Strip Curtains 17 3 UES measures given provisional status on 8/3/2010 Sunset date set as 8/3/2011 A request was made at that time to investigate the measure impact on door open time First rebate issued 11/30/2010
Strip Curtains 18 PECI has installed meters at 6 locations to collect door open times pre/post implementation Initial results: not statistically valid In the meantime: New UES guidelines PECI proposes: extend sunset until it undergoes RTF subcontractor review
Your consent to our cookies if you continue to use this website.