Presentation on theme: "Introduction Todays presentation will cover the following topics:"— Presentation transcript:
1Introduction Todays presentation will cover the following topics: Session 1Intruder Alarm SystemsCCTV (Closed Circuit Television) SystemsAccess Control/Door Entry SystemsQuestions & AnswersTea Break (approx. 10:30am)Session 2Fire Detection & Alarm SystemsEmergency Lighting Systems
2StandardsAll of the systems that we will cover today are regulated and covered by the standards indicated belowNSAI – National Standards Authority of Ireland PSA – Private Security AuthorityIntruder Alarm Systems – EN :2006 (NSAI & PSA)CCTV Systems – PSA2006_12 (NSAI & PSA)Access Control – SR40 (NSAI & PSA)Fire Alarm Systems – IS3218:2009 (NSAI)Emergency Lighting Systems – IS3217:2008 (NSAI)
3Regulatory Bodies NSAI – National Standards Authority of Ireland PSA – Private Security AuthorityThe NSAI are the most commonly used regulatory body in relation to Intruder Alarm Systems although there are others such as EQA, MSC, SSAIB, CerticCS & Stellar Certification Services.In the case of the NSAI, certification is provided and continually audited and renewed via annual inspections of certified installations.The PSA will issue a licence in relation to Intruder Alarms, CCTV and Access Control based on a combination of Certification from one of the bodies indicated above along with further information provided to them by the company in question.The PSA was established in 2004 pursuant to the Private Security Service Act, 2004 to provide further regulation of the Security Industry covering Intruder Alarm Installation & Maintenance, Remote Monitoring, Static Guards etc. It is the statutory body with responsibility for regulating and licensing the Irish private security industry. It provides a national database of licenced contractors which is readily accessible on line.For users of private security services, Section 38 of the Act makes it an offence to employ an unlicensed security contractor or employee. Contravention Section 38 of the Act will make a person liable to incur a fine of up to €3, and/or imprisonment. The penalties for unlicensed contractors is similarly harsh.The PSA application procedure requires Garda vetting of all company directors going back to their original place of birth including all places of residence.In the case of other company employees, Standard SR40 requires an employer to review a prospective employees history for the previous 10 year period including employers, schools, work abroad etc. This can be reassuring for prospective clients considering the types of system being installed and maintained by the company.
4Alfa Security Ltd Company Background Alfa Security Ltd was established and registered in 1984.Started out installing and maintaining both domestic an commercial intruder alarm systems to IS199 which was the standard of the day. This standard has now changed to EN :2006.Have kept apace with the industry and expanded to also cover CCTV, Access Control, Door Entry, Gate Automation, Fire Alarm and Emergency Lighting Systems.Work at the cutting edge of all new technologies, best practices and standards offering systems of all scales to suit Customer, Site and Budget.Can offer a security consultancy service to existing and prospective customers at no cost including system reviews and security audits.In the early days before technology really took off, alarm systems could be installed with a series of relays, power supplies and a few magnetic contacts.We had devices like pressure mats under carpets, CC Wiring on Doors and Foil Tape on Windows.The industry has changed so much since then that technology and its advancements are at the forefront and are constantly evolving.I have to say that given we are in the grip of a recession and the amount of new trade is slower, January started the year for us on a very positive note. We have a strong and loyal customer base and our emphasis is on customer service and system/site audits. It is quite amazing the number of devices that fail on inspection and if a system is not regularly maintained/serviced, this can go unnoticed for a long period.A few examples of our audit/review findings:Circuit Court Judge – We had taken over the maintenance of the alarm system and had carried out an alarm upgrade along with the installation of a CCTV System. During our post installation follow up call we called to the site and recommended the installation of an additional alarm keypad on the upper floor. It was pointed out to the customer that the last thing you need is to come downstairs to the alarm keypad in the event of an activation. On the garden perimeter there was a full automated set of swing gates which offered a good level of security but this was then complemented by a low wall and sparse hedge. At times you must assume the mentality of the burglar in order to identify the areas of risk.
5Intruder Alarm Systems Standard: EN :2006Installers require certification/licencing from the following bodies:NSAI (National Standards Authority of Ireland)PSA (Private Security Authority)
6Areas to be covered include: System DesignSystem Types including Pros and ConsBasic System Principles – Perimeter Protection, Trap ProtectionBasic Detector TypesCommunications EquipmentAlarm MonitoringCertification & WarrantySystem Maintenance
7System DesignSystem Design is based on but not limited to the following:Purpose of SystemCustomer RequirementsSite History & LayoutType of BusinessOverall Site Risk AssessmentAccessibility of SiteBuilding ContentsTypes of Doors/Windows etcBuilding Contents & Value
8System Types Hard Wired vs. Wire Free Intruder Alarm Systems can be Hard Wired, Wire Free or a mixture of both. There are a wide range of detectors available for both types of system and each type will have pros and cons depending on the site and the overall system requirements.Panels on the market can be hard wire only, wire free only or hybrid which offers a mixture of both technologies
9Hard Wired Systems Pros No RF Range issues No device battery replacement costsWider range of detection equipment availableConsCabling can be labour intensiveNot suitable for some finished buildings
10Wire Free Systems Pros No cabling required Very easy and quick to installMinimum site disturbanceCan have similar cost to wired systems in some applicationsConsRF Range of Detectors can be limited depending on building, construction materials etc.Batteries need to be replaced every 2 yearsAs technology improves, we find that battery life also increases
11Basic System Principles Perimeter Protection – Protection of windows and doors by way of Inertia Shock Sensors, Magnetic Reed Contacts, Combined Shock Sensor/Magnetic Contacts, Point to Point Beams and External Motion Detectors.Trap Protection – Protection of Internal Areas by way of motion detectors.Full Protection – Carried out by a combination of the above.Our philosophy has always been to offer full protection whereby the entire perimeter is protected including all window opes along with internal trap protection by way of Motion Detectors
12Basic Detector TypesMagnetic Reed Contact (MC) – These devices detect a physical opening only and are normally used on windows and doors.High Frequency Inertia Sensor (SEN) – These devices operate by detecting vibration. They are used on windows and doors to detect a forced entry/breakage.Combined Sensor & Contact (COM) – These devices are a combination of the above.Passive Infra Red Detector (PIR) – These devices detect changes in temperature of the type generated when a person crosses their field of view.Dual Technology Detector (D-TEC) – These devices contain two different detectors in one unit which must be activated simultaneously before an alarm condition is signalled. They normally consist of Ultrasonic, Passive Infra Red and Microwave Detection technology.Microwave Detector (M.WAVE) – These devices detect microwaves and are normally used in warehouses and large open plan areas. They offer vastly improved detection range when compared with PIR or D-TEC.Transmit/Receive Beam (TX/RX) – This is a set of beams which include an infra red transmitter and receiver or reflector unit. This are used to detect movement between two set points.
14Communications Equipment PSTN Digital Communicator – This unit is fitted to the Intruder Alarm Control panel and connected to a telephone land line to allow signals to be sent from the Alarm System via the phone line.GSM Communicator – This can be used in the absence of, or in addition to a land line based communicator. These units operate on the GSM Cellular Network and can be used as a stand alone communicator or as a back-up device to the PSTN Communicator.Mesh Radio Communicator – These units operate on Radio Frequency to allow signals to be sent to the Alarm Receiving Centre only. These are far more secure than both the PSTN and GSM Units.The majority of communicators on the market today offer Text Messaging, Voice Messaging and Central Station Monitoring capabilities.In some cases, the GSM Unit can also be controller via text message allowing a user to set/unset the system, check recent events and also (via relays) control lighting, heating, gates etc.
15Alarm MonitoringAlarm Receiving Centre (ARC) – Alarm signals are sent to an approved ARC who in turn contact the nominated keyholders and/or Gardaí as required. Garda response requires that the Alarm System has some form of verification technology in place such as Audio or Video Verification. In most cases alarm verification is carried out by the alarm system when a second separate detector activates. This service carries an annual charge.SMS Text Messaging – In the event of an alarm activation, a text message is sent to nominated mobile phone numbers. (SMS Text Messaging is not available with UPC telephone lines)Voice Messaging – In the event of an alarm activation, the alarm system dials the nominated phone numbers in sequence with a pre-recorded voice message.Standard Monitoring fees would be as follows:Domestic (Landline Based) - € inc Vat per annumCommercial (Landline Based) – € plus Vat per annumRadio/GSM Backup (supplied by ARC) - € € plus Vat per annumIn the event of the installation of a third party GSM unit such as HKC, Pyronix etc, there is also a SIM Card cost to be considered (normally in the region of €10.00 per month.Copies of the Intruder Alarm Completion Cert are provided to the Client, ARC and certification body. On completion of all required paperwork, the Gardai issue a URN (Unique Reference Number) for the site. This is a requirement for Garda response to monitored systems.
16Certification & Warranty All equipment installed comes with a 12 month manufacturer’s warranty.On completion of an Intruder Alarm System, a certificate of compliance to EN is issued. This certificate remains valid for 12 months from the date of installation. To maintain the validity of this cert, the customer must have a maintenance contract in place with a licenced company.
17System MaintenanceIt is a requirement under EN , to have a maintenance contract in place to retain the validity of the certification.It is best practice to have contract in place to have the Intruder Alarm serviced bi-annually at approximate intervals of 6 months.Maintenance contracts normally include access to a 24hr Emergency Service, preferential call booking along with reduced call out charges.It is the client’s responsibility to ensure that the system is maintained/repaired as required.
18ReviewI would hope that this presentation has provided you with a better understanding of Intruder Alarm Systems and I am now open to answer any questions that you may have.
19CCTV Systems Standard: PSA2006_12 Installers require certification/licencing from the following bodies:NSAI (National Standards Authority of Ireland)PSA (Private Security Authority)
20Areas to be covered include: System DesignSystem TypesCamera TypesImage QualitySystem NetworkingMonitored CCTV SystemsSystem WarrantySystem Maintenance
21DefinitionA Closed Circuit Television (CCTV) System is a system of electronic or other devices designed, constructed or adapted to monitor or record images on, or in the vicinity of a premises.
22System DesignSystem design should be based on but not limited to the following:Customer RequirementsSystem purposeSite specific risk assessmentData Protection and Privacy LegislationStages of CCTV Design & InstallationLocation Survey/Site Plan/Risk AssessmentSystem DesignSystem Design Proposal (SDP) DocumentInstallation PlanningSystem InstallationTesting & CommissioningAs Fitted Document (AFD) provided to clientTechrete (example) approx 13,500 sq mt – System was originally designed for a new building but was not reviewed in relation to the changes in site layout/usage. Stock, racking etc was installed around the perimeter of the building obscuring CCTV images and the external motion sensors. Images at night were very poor due to a combination of camera and lighting quality.This was vastly improved with the installation of a Full Function Dome camera at high level which has a zoom ratio of 18:1 with on-board infra red LEDs with a range of 70mt.
23System TypesCCTV Systems are divided into two main types as outlined below: Conventional Digital System This type of system consists of analogue CCTV Cameras which are connected to a Digital Video Recorder (DVR) which stores the required images on an Internal Hard Disc Drive. Cameras are connected to the recording equipment via Coaxial Cable and BNC connectors. The DVR comes in 4/8/16 & 32 Camera configurations. IP Based System This type of system consists of IP CCTV Cameras which are connected to a Network Video Recorder (NVR) which also stores the images on an Internal Hard Disc Drive. Cameras are connected to the recording equipment via Cat 5e/Cat 6 Data Cable. IP Cameras offer far superior image quality to that of analogue cameras and the systems are more flexibility when compared to analogue systems.Equipment costs have been constantly changing/reducing over the past few years in the case of both types of systems as the required technology becomes widely available and new manufacturers enter the marketIn the case of a standard 4-camera IP System, the equipment costs can be anywhere from % more expensive depending on requirements.
24Analogue Systems Pros Equipment is relatively inexpensive Huge range of equipment/manufacturer’sTried & Trusted technologyConsA finite number of cameras can be connected to a single DVRLimited image resolutionInstallation of cabling can be labour intensive
25IP Based Systems Pros Far superior image quality More flexible than an analogue systemLess cabling required when using Hubs/SwitchesMore functionality in relation to search/archivingConsEquipment is far more expensiveMore Hard Disc space required due to higher quality images.Smaller range of camera types/manufacturer’s
26Camera TypesCCTV Cameras will normally be Monochrome only, Colour only & Colour/Mono and are available in a wide range housings.Fixed Box Camera & Lens – These are normally mounted internally on brackets or inside an externally rated housing. The camera comes with a separate lens which is interchangeable.Internal/External Dome Camera – These come with a built-in lens which can be fixed or varifocal type.External Bullet Camera - These come with a built-in lens which can be fixed or varifocal type and normally have built-in Infra Red LED to provide a monochrome image in low lighting conditions.Covert Camera – These are usually in the guise of an Intruder Alarm Motion Detector or a Smoke detector unit although other types are available and they are not readily identifiable as a CCTV Camera.Full Function Camera – A full function or Pan/Tilt/Zoom (PTZ) camera is a camera which can be controlled via the CCTV Recorder, Joystick or Network Connection. These cameras can be fully controlled to view various areas within a site and are especially useful on sites where there is an operator in control of the system at all times.There is an enormous range of cameras available with different styles, lens & IR ranges and configurations, these are just some of the main examples.Day/Night or Colour/Mono Cameras automatically change from Colour to Black & White once the lighting levels have dropped below the cameras threshold.
27Camera Types Box Camera Camera Housing Dome Camera Bullet Camera Covert CameraFull Function Camera
28Image QualityImage quality is determined by a number of factors such as:Recording EquipmentCamera type & performanceAvailable lightThe standard PSA2006_12 provides for minimum image sizes in relation to various requirements as follows:Monitoring – The target shall represent not less than 5% of the picture heightDetection – The target shall represent not less than 10% of the picture heightRecognition - The target shall represent not less than 50% of the picture heightIdentification - The target shall represent not less than 120% of the picture heightMajority of DVRs and NVRs have the facility to alter the image resolution, quality and frame rate per camera. For example a system can be set up to constantly record low quality images at 6 fps, once the camera or external trigger detects motion, the system can be set to record a high quality image at 25 fps, thus saving on HDD spaceAvailable light has a huge bearing on the final images produced by any CCTV Camera and levels on site should be checked using a Lux Meter at the initial Risk Assessment/Survey Stage
29System NetworkingThe vast majority of both analogue Digital Video Recorders and IP Network Video Recorders can be networked to allow for remote access to the CCTV System via Local Area Network (LAN) or Wide Area Network (WAN).Remote access can be via Desktop PC, Laptop, Netbook, Tablet PC and Smartphone. Offsite access will require a Broadband Connection at the recording equipment.In the case of tablet PC and smartphone, remote access would normally involve the installation of the relevant App.If the system has been networked for remote access, an amplifier and speakers can also be connected allowing for audio commands/warnings to be issued via the CCTV System. This can be done from PC, Smartphone etc.
30Monitored CCTV Systems CCTV Systems can be remotely monitored by Alarm Receiving Centres (ARC) with the additional of external Motion Detectors and PA Speakers. The Motion Detectors trigger an alarm condition to the ARC and in some cases will also send a video clip of the cause of the trigger. ARC operators can then take a live view of the system and issue audio alerts to site via the external speakers. This type of system makes a huge difference to sites as in the vast majority of instances, the unauthorised person leaves the site immediately.Monitored CCTV Systems have proved to be a huge success, especially in the case of a client who cannot afford to have manned security on site. Whilst the installation costs can be quite high, the savings over the course of a year can be huge.The most obvious advantage of a monitored CCTV Systems is that it is a very effective deterrent. In the majority of cases, once an audio warning is issued, the unauthorised persons leaves the site
31System WarrantyThe vast majority of components installed as part of a CCTV System will come with a 12 month warranty although this may be up to 5 years depending on the equipment installed and the manufacturer.
32System MaintenanceTo retain the validity of the certification issued, a customer is required to have a maintenance contract in place with a licenced company.Systems should be serviced bi-annually at approximate 6 month intervals.It is the client’s responsibility to ensure that the system is maintained/repaired as required.
33ReviewI would hope that this presentation has provided you with a better understanding of CCTV Systems and I am now open to answer any questions that you may have.
34Access Control & Door Entry Systems Standard: SR40:2005There is a requirement for the installer to have SR40 certification from the National Standards Authority of Ireland (NSAI) along with the relevant licence for Access Control from the Private Security Authority (PSA)
35System OverviewAccess Control/Door Entry Systems are designed to limit access to a premises to Authorised Persons Only. This can be carried out by use of Audio or Video Intercoms, Access Keypads, Swipe Card Readers, Proximity Readers and Biometric Readers. Systems can be interlinked with Intruder Alarms Systems, Fire Alarm Systems and CCTV Systems as required by the client.
36System DesignAccess Control Systems are designed based on the customer requirements.Safety considerations must be made in relation to the type of locking device used, it may be Fail Safe (the door releases on loss of power) or Fail Secure (the door remains locked on loss of power)Push to Exit Buttons and Green Manual Call Points are generally located on the secure side of the door in question although these may be substituted with a further access control readers as required.
37Door EntryDoor Entry Systems are can be a basic Intercom System with Audio Only which controls an electronic lock with a release button on the Intercom Handset to more complicated Video/Audio Systems with multiple entrances and Answer Stations.These systems are designed to allow the client to check/interrogate callers to a premises before granting access.
38Electronic Access Control Access Control Systems are installed to allow authorised persons to access areas of a premises via Keypad/PIN Number, or Proximity Cards/Fobs.These systems can be stand-alone type or fully networked systems which are controlled via centralised PC and Software.Access Software allows for the system to be set up for access during certain hours, to certain doors, for certain people. It can also be used to provide Muster Lists, Time & Attendance Records or to historically track usage of doors/users.Core TimesUser GroupsDoor GroupsVisitors
39Access ReadersKeypad – This is operated by inputting the allocated PIN/Code Number which allows the electronic locking device to release the relevant access point (Door/Gate/Turnstile etc.)Swipe Card Reader – This is operated with an Access card which contains a Magstripe which is swiped through a slot in the reader unit.Proximity Reader – This is operated by presenting a Proximity Card or Fob to the Reader. This units do not require that the Proximity Card/Fob actually touches the reader unit thus preventing the wear and tear normally seen with Swipe Cards.Biometric Reader – Also known as a Fingerprint Reader, this is operated by presenting the persons index finger to the reader unitPIN Keypads and Proximity readers are the most popular means of access control at present although Biometric Technology has become more reliable and less expensive over the last few years.Anti Pass Back
40Access ReadersMagstripe/Swipe cards are old technology and are subject to wear and tearProximity readers can be used with proximity cards or fobsBiometric readers operate by recognising the unique fingerprint of the individual.
41Locking OptionsAccess Control Systems would normally be installed in conjunction with some form of Electronic Locking Device such as Electromagnetic Locks, Electronic Solenoid Drop Bolts, Electric Strike Locks, etc.It is best practice to link these systems to a Fire Alarm System (if present) to allow the relevant doors to automatically release in the event of an Fire Alarm System activation.MaglockDrop BoltElectric StrikeCISAAbloy
42System MaintenanceIt is best practice to have an Access Control System serviced Bi-Annually at approximate 6-Month intervals.All readers, doors, locks, power supply units and batteries should be checked during the course of these visits.
43ReviewI would hope that this presentation has provided you with a better understanding of Access Control & Door Entry Systems and I am now open to answer any questions that you may have.
46Areas to be covered include: Purpose of SystemSystem DesignSystem CategoriesSystem TypesBasic Detector TypesSiting of DetectorsAudible & Visual EquipmentCommunications EquipmentAlarm MonitoringCertification & WarrantySystem Maintenance
47Purpose of SystemThe primary function of a Fire Detection & Alarm System is to provide an early warning of a Fire in the building in order to alert the occupants thus increasing their chances of escape.A secondary function of the system is to reduce loss of, or damage to the property thus increasing the chances of extinguishing the Fire.These systems can be linked to other applications and services in the building such as Gas Slam Valves, Smoke Vents, Access Control Systems, Intruder Alarm Systems etc.
48System DesignSystem Design is based on but not limited to the following:Purpose of SystemCustomer RequirementsSite History & LayoutType of BusinessOverall Site Risk AssessmentAll stages of system design should be carried out in conjunction with IS3218:2009.Fire Officer Recommendations/RequirementsAccessibility of SiteBuilding ContentsBuilding UsageBuilding Contents & Value
49System CategoriesCategory M Systems – These offer no automatic detection devices and comprise Manual Call Points and Sounders Only.Category L Systems – The primary purpose of a Type L System is the protection of Life and this can be sub-divided in further sections based on the overall level of protection offered (L4, L3, L2, L1)Category (M or L)X Systems – This type of systems denotes a building with Multi Occupancy.Type M Systems require Manual Initiation of an AlarmType L System – Includes automation detection equipment. Category L Systems shall always contain a Category M SystemL4 – Protection of escape routes onlyL3 – Protection of Escape Routes & Adjoining AreasL2 – This is a Category L3 or L4 supplemented with additional protection in specific areas (noted as Category L2/L3 or L2/L4)--X – In multiple occupancy buildings there may be a requirement to link separate fire panels or provide audible and/or visual indication of a fire condition in other parts of the premises.
50System TypesConventional System – This type of system is based on separate zones which have multiple detectors installed. On activation of the system, the control panel will indicate the activated zone only. The user must then physically check each detector on the zone for activation.Addressable System – This type of system consists of individually addressed detectors and/or sounders which are connected in a loop. On activation, the control panel will show the device address along with a device location.Conventional Systems can be less expensive to install due to the cost of the equipmentAddressable systems offer far superior indication of the exact location of an alarm activation but the equipment is more expensive.Callouts by Fire Services can cost between €100-€
51Detector TypesFire Detection & Alarm System will normally comprise of some or all of the detection devices indicated below.Manual Call Points – Manually Activated by personsSmoke Detector Units – These are mainly two different types, Ionisation or OpticalHeat Detector Units – These can be Rate of Rise or Fixed TemperatureOptical Beam Detector Units – These are normally used for larger areas such as warehousesFlame Detector Units – Detect Ultraviolet or Infra Red radiation usually put out by firesCarbon Monoxide Detector – Used to detect CO2 in areasIonisation Detector – Based on the principle that the electric current flowing between electrodes in an ionisation chamber is reduced when smoke particles enter the chamberOptical Detector – The operate by detecting the scattering or absorption of light by smoke particlesFixed Temp Detector – These operate when they reach a pre-selected temperature thresholdRate of Rise Detector – These operate when the temperature rises abnormally quicklyOptical Beam Detector – These comprise a transmitter and receiver/reflector unit. They operate by detecting changes in the beam signal due to smoke particlesCarbon Monoxide – CO2 can be generated by smouldering or slow burning fires.
52Detector Types Fire Bell Conventional Panel Firetuff Cable Detector BaseDetector HeadManual Call Point - Reset TypeElectronic SounderManual Call Point – Break Glass TypeFire Gland
53Siting of DetectorsFire Alarm Detectors should be installed in accordance with both IS3218:2009 and manufacturer guidelines.Average Coverage is as follows:Heat Detector – 50 sq. mt, max distance between centres 10 mtSmoke/CO2 Detector – 100 sq. mt, max distance between centres 12 mtSiting of detectors will be dependant on the original site survey/risk assessment and will be based on other factors included in IS3218:2009
55Audible & Visual Equipment An audible and visual device shall be located externally on the building in order to guide fire fighting assistance to the correct entrance to the building.Systems should comprise 2 no. Sounder Circuits with a minimum of 2 no. Audible Devices staggered throughout the premises to achieve a minimum level of 65db or 5db above any other noise which is likely to persist for more than 30 seconds.Where the audible devices are required to wake sleeping persons, the required level is 75db at the bed headIn music venues where the music is at 80db, the fire alarm system shall mute the music on activation.
56Communications Equipment Fire Alarm Systems can have there own stand-alone communication devices operating on PSTN, GSM or Radio technology. In the majority of cases the Fire Alarm System is linked to an Intruder Alarm System on site for the purpose of remote monitoring.PSTN Digital Communicator – This unit connected to a telephone land line to allow signals to be sent from the Alarm System via the phone line.GSM Communicator – This can be used in the absence of, or in addition to a land line based communicator. These units operate on the GSM Cellular Network and can be used as a stand alone communicator or as a back-up device to the PSTN Communicator.Mesh Radio Communicator – These units operate on Radio Frequency to allow signals to be sent to the Alarm Receiving Centre only. These are far more secure than both the PSTN and GSM Units.
57Fire Alarm MonitoringAlarm Receiving Centre (ARC) – Alarm signals are sent to an approved ARC who in turn contact the nominated keyholders and/or Gardaí as required. Garda response requires that the Alarm System has some form of verification technology in place such as Audio or Video Verification. In most cases alarm verification is carried out by the alarm system when a second separate detector activates. This service carries an annual charge.SMS Text Messaging – In the event of an alarm activation, a text message is sent to nominated mobile phone numbers. (SMS Text Messaging is not available with UPC telephone lines) (Only available when connected to an Intruder Alarm System or via GSM)Voice Messaging – In the event of an alarm activation, the alarm system dials the nominated phone numbers in sequence with a pre-recorded voice message.There is no all encompassing legal requirement to have a Fire Alarm System monitored remotely although it would be considered to be best practice.A lot will depend on the Fire Officer and Insurance Company requirements
58Certification & Warranty All equipment installed comes with a 12 month manufacturer’s warranty.On completion of an Fire Alarm System, a certificate of compliance to IS3218:2009 is issued indicating the relevant category of system.A Fire Alarm Log Book must be kept on site at all times and all routine service calls, faults, repairs and tests must be logged.
59System MaintenanceA Fire Alarm System should be visually checked on a daily basis, and at least one device should be activated on a weekly basis by a responsible person nominated by the client.A quarterly test should be carried out by a competent company during the course of which, 25% of all devices are tested such that at the end of the annual period, 100% of the system has been tested.
60ReviewI would hope that this presentation has provided you with a better understanding of Fire Alarm Systems and I am now open to answer any questions that you may have.
61Emergency Lighting Systems Standard: IS3217:2008fghf
62Purpose To clearly indicate the escape route To provide illumination along such routes to allow safe movement towards and through the exists provided.To provide sufficient lighting to enable the emergency services to conduct a search and rescue.To illuminate Fire Fighting Equipment and Call Points.To provide lighting for the premises to be reoccupied.
63Types of SystemCentral Battery System – This type of system is powered by an array of batteries which are located remotely from the actual emergency lights.Self Contained System – This type of system utilises individual emergency lights which contain their own backup battery pack.Self contained systems would be more widespread than central battery typeCentral battery systems are more costly to maintain, replacement fittings are more expensive and not as readily available, battery replacement costs can be hugeBasketball Arena – System was only linked for full mains failure which meant that the arena lights could trip out and no E/L would come on. This was rectified by linking the system to all lighting circuits so that a circuit tripping would bring on all emergency lights
64Types of FittingsNon-Maintained – These fittings will only illuminate in the event of a loss of mains power.Maintained – These fittings are constantly illuminatedSustained – These fittings are constantly illuminated and have two separate lamps, one which operates on mains power and a second which operates on battery power.Fittings can be stand-alone such as Exit Signs and Emergency Bulkhead type fittings, Twin Spot Type fittings or can be standard light fitting which have built-in emergency Invertor Packs.
65Emergency Light Locations Exit Signs – These should be Maintained Type fittings and are located to indicate a route to, and to show final exits from the premises.Emergency Lights – These are Non-Maintained Type fittings and are located along escape routes, at changes in direction or floor level, above stairs and at locations where a person must be able to safely turn off any required equipment which may cause a hazard if not supervised when power is restored.Twin Spot – These are normally used to cover larger areas such as assembly areas, production areas and warehouses.
66Installation NotesEmergency Lighting should be installed in accordance with the current standard and manufacturer’s recommendations.Average height of luminaires is a minimum of two metres above floor level.Building layout/finish must be taken into consideration when designing or installing an Emergency Lighting System to take in such factors as building use, light reflection, minimum light levels required etc.
67Certification All certification must include the following details: The design/installation/commissioning company details.Designers name, signature and qualification detailsInstallers name, signature and qualification detailsCommissioners name, signature and qualification detailsStatement to the effect that the design, installation and commissioning of the system is in accordance with I.S.3217:2008Statement from the Designer/Installer that they are suitable qualified to carry out the worksDetails of the premises including fulled marked, as built drawings.
68Testing/ServicingEmergency Lighting System can be tested by utilising a Central Test Unit which can be located on the Distribution Board or as a Stand-Alone Unit. These units mimic a loss of mains power to the relevant luminaires for durations of half hour, one hour and three hour intervals.Emergency Lighting Systems should be tested by a responsible person on a quarterly basis with at least one full three hour test carried out per annum.An Emergency Lighting Log Book should be kept available on the premises and all tests, services, faults and repairs should be logged.
69ReviewI would hope that this presentation has provided you with a better understanding of Emergency Lighting Systems and I am now open to answer any questions that you may have.